Frequently Asked Questions
No, the Leading Edge dimmer has a maximum input capacitance of 300nf, you would be able to use the 31LCDA as an alternative.
Trailing Edge and C-Bus Universal dimmers do not have a capacitance limit and either can be used.
The rating of the 31CAP is 10nF (Nanofarads).
The minimum load for a 2 wire infrascan is 40W. If the load is less than this you can use a 31CAP wired in paralel across the load.
Yes, it can but you will need to put a 31CAP in parallel with the load.