Frequently Asked Questions
No they don't fit. You will need to replace the old MG MCB with new Acti9 MCB to fit the new Auxiliaries
No. Unfortunately it does not and we don't do the terminal Shiels for iDPN N vigi as the screws are small.
No, those are designed to fit onto the acti9 AC MCBs for those MCBs use the A9N26929
The ref A9N18359 is C120 MCB (Multi9 design in the white material).
The ref A9A26924 is iOF auxiliary (Aciti9 design for iC60 MCB).
I can confirm that the parts A9N18359 and A9A26924 are not compliant with each other
the Acti9 A9A26970 will fit on the domae breakers.
Yes, that is designed to fit on the Acti9 shaped devices including the iSW switches.
A9Z51240 = Type B single phase RCCD
A9F54240 = 2 pole, 40A, Curve MCB
A9A26969 = Under voltage release
Yes, A9A27006 is suitable to use on A9S66463
No , can't uses the locking device in ON position.
30VA In Rush
4.5 VA Sealed