The alternative Acti 9 conversion is the A9F45316 3 Pole 16A 6kA MCB
The Acti 9 Breakers can work up to 440 VAC as per typical data sheet
The A9F44140 is the Acti 9 substitute.
Please see the attached datasheet for further information on the A9F44140.
Part code 25815 Multi 9 - Acti 9 A9F44206
See attachment of conversion chart for Cross Reference from Multi 9 to Acti 9
Request to field install a fingersafe cover on a Multi 9 breaker in the field.
Multi 9 C60 Breakers
Applies to Multi 9 breakers.
An installed Multi 9 breaker needs fingersafe guards.
The fingersafe cover can only be factory installed on the Multi 9 C60 breakers by adding an "F" to the end of the catalog number..
This item is not available in 9 way. You can purchase a 10 way the part number is B10/30/5-WE which is an indent item.
Domae is for Domestic, the Multi 9 or Acti 9 is for commercial/industrial
Yes they will fit as they are standard din rail mount breaker.
No, Acti 9 MCB's are not available in a 5 amp frame size.
Unfortunately. The part number 755H is no longer available.
140ACI03000 requires 9 words of addressing. The 9'th word is a status register used for over range/ broken wire indication.
No, only Square D breakers will fit to the Square D chassis and vice versa, this is due to the special mount requirements.
The part number for Acti 9 breaker , 3 pole, 40A, 10KA is A9F54340
For more information see:https://eshop.schneider-electric.com/product.aspx?org=21&lang=1&dist=276&prod_id=A9F54340
Schneider does not publish a trip curve for Acti 9 MCB. However, it is confirmed that they comply with the standards IEC 61008, IEC 61009 and AS/NZS3190:2002 Type II.
The maximum break times for these standards are outlined in the document attached with advise on discrimination with RCD devices.
The replacement is the Acti 9 A9D11820
Model | Current Rating | No. of poles | Sensitivity | Width in mod. of 9mm
iC60H* | 20A | 1P + Ns | 30mA | 2
No there is no 10mA RCBO's with in the multi 9 range
The replacement is a Acti 9 A9C20863
IDPN N VIGI 20A C 30MA A-TYPE RESIDUAL C
All Acti9 RCCB's are rated 230-240v AC only
The part code is A9C30211
ATV58 control board pinout 10 pins vs 9 pins? What is the difference?
All serial numbers
Not sure which pins to use.
10 pin terminal has an additional AO1 terminal located on the left side (not used) . Use the 9 pins on the right side of the terminal strip.
See attached wiring diagram. Modbus serial link - L = 2.5 m - 1 female SUB-D 9 + 1 male SUB-D 25
The magnetic tripping threshold of the Acti 9 and older Multi 9 circuit breakers is higher than in alternating current. The magnetic tripping threshold is determined based on the attached documents.
What is the tripping current for a Multi 9 GFP Ground Fault Protector?
Multi 9 C60 Ground Fault Protectors
Tripping currents are as follows:
GFP30 Must trip at 29.9 mA; must not trip below 22.1 mA
GFP100 Must trip at 98.9 mA; must not trip below 73.1 mA
GFP300 Must trip at 299 mA; must not trip below 221 mA
Can Multi-9 C60 breakers be continuously loaded to 100% of their rating?
Multi 9 C60 MCB's
UL 489 Listed Multi 9 C60 circuit breakers may be loaded to no more than 80% if used with continuous loads.
UL 1077 recognized supplementary protectors may be operated at 100% of their rating.
IEC 60947-2 C60 breakers may be operated at 100% of their rating.
CTA-ID : 5437
The Domae range is desigened for domestic applications its raings are 6KA C curve single phase 6Amp to 40Amp
Our Commercial offer is Acti 9
To warn people that even if it is bottom fed the electronics are still live
Not available as a spare part
The DBFNE9 is available as Neutral Earth bar 9 way is available as a spare part
It is available in acti 9 range:
A9E18074 which is 20A 250V rated.
Please see attached wiring diagram.