You can purchase PDL 695X and the pdl indicator module that is required
The cover to suit the PDL 695 is a 695C.
The part number is PDL695CWH
Use a PDL695X and put a PDL600SM in the extra mech space
PDL has a small surge mdoule which can be installed into any 600 series switch hole.
600 series Surge Module Surge Protection
No the PDL 695R is only available in white - PDL695RWH
As a general rule of thumb -
PDL items require PDL at the front of the code.
600 series item codes start with 6.
600 series switch codes start with 68.
The number of switches fitted in the plate is the 3rd number in the code, 681 = single 600 series switch, 682 = double 600 series switch
600 series socket codes start with 69.
The 3rd digit in a socket code indicates the type of socket, 691 = single vertical socket, 692 = double vertical socket, 694 = single horizontal socket, 695 = double horizontal socket.
Most codes require a colour code at the end, WH = white, BK = black.
eg. To order a black double vertical switched socket the complete code would be PDL692BK.
800 series (Modena) item codes start with 8 and follow the same format as above. (800 series items with Strato plates start with S8...)
eg. An 800 series Modena double switch in white = PDL882WH, a Strato double horizontal switched socket in black = PDLS895BK
In both series metal cover plates are an extra option to be supplied separately, coded to fit the plate required, eg. 600 series single switch metal plate in Stainless Steel = PDL681MSS (M = Metal, BBZ = Brushed Bronze, PB = Polished Brass) Some plastic cover plates are available eg. PDL681CWH (C = Cover), PDL800PSCH (PS = Plastic Surround, CH = Champagne, there are 9 colour options in 800 series)
Strato brushed aluminium plates also need BK or WH to decide the trim colour, eg. PDLS800CBABK or PDLS800CBAWH (C = Cover , BA = Brushed Aluminium)
Module grids with covers are available in BK or WH, eg. PDL684VHWH (VH = vertical/horizontal since the grid is empty and module can be fitted either way), PDLS800GPSBK (GPS = Grid, Plate, & Surround).
Grids without covers included are only available in Modena 800 series, PDL800G (horizontal) or PDL800GV (vertical)
Refer pdl.co.nz for further details and options.
No, we have no 15A sockets available with an extra switch.
No, the complete unit does not come complete in black. However, you can purchase the PDL 695C in black (BK) and swap the cover plates over.
But the Sockets and the switches will still be white.
The part number for your 6.5 inch bluetooth speakers is 5600ICBT65.
Configuration is different
699 - switch, socket, socket, switch
699TB - switch, socket, switch, socket
Plate 48mm (H) x 170mm (W)
Mounting Centres: 150mm
Suits PDL 567L mounting Block & PDL 559 Mounting Bracket
No - Rated at 15A = PDL694/15WH
Meaning of Trip Classes for overload relays.
NEMA Overload Relays
North American Products
The trip class means that at 600% (6 times) of the maximum thermal current rating (or 600% of the actual dial setting on adjustable overloads) the Class 10 will trip in 10 seconds or less, Class 20 will trip in 20 seconds or less, and Class 30 will trip in 30 seconds or less.
RM 79 696 043: operating temperature.
The maximum operating temperature is 60°c.
Legacy KB System (APS) Data: RESL197838 V1.0, Originally authored by LaBe on 02/18/2009, Last Edited by LaBe on 02/18/2009
Related ranges: Zelio Control
The PDL675 shaver outlet is rated 20VA @110/230 volts.
The 685 and the 686 take the same coverplate so the code is the PDL686MSS (for stainless steel)
Yes, as long as the combination doesn't exceed the 625 specifications.
Can be ordered using the following codes:
PDL395G + PDL395C-AN
There is no 800 Series equivalent shaver socket
800 series only has an RCD
Not available in red as a cover only, can purchase the complete unit in red (PDL 691RD)
There is no metal cover available for the 699 There is only a metal cover for the 699TB version
No, They are not available in Ivory colour.
Yes, that is switched on as the plug is inserted.
You can plate mount a surge module PDL600SM into any 600 series aparture that could be a 681VH plate or a 695X
Looking for the watts loss on a ATS48 soft start, for calculating heat loss, for enclosure sizing.
Altistart ATS48 soft starters
Needs to know the dissipated heat loss in watts the ATS48 soft starter will produce when running at full load.
See the table below and choose the ATS48's watt loss based on if a shorting contactor is being used or not.
If Error 195 appears on the front panel of an ION7650 or ION7550 meter upgrading to the latest firmware (v352) will resolve this issue.
Date Created: October 30, 2008
Last Revised: May 1, 2009
Original Author: MN
All content © 1992-2009 Schneider Electric
The 4 inch is 85mm high and the 6.5 inch is 80mm.
F695 is the High Frequency setting for the Analog Output but the factory setting is 0
ATV21 and ATV212
All models and serial numbers
In fact when F695 = 0hz it acts for the scaling using FH (maximum frequency), so if you have set a different value of FH than 50Hz or 60Hz and your motor is running at 50Hz for nominal speed, you have to adjust this parameter for scaling
User wants to use three phase 120V L-N through a potential transformer for control power to the CM4000 that is 69V L-N
|Yes, the circuit monitor can be used with line-to-line rated PT's connected line to neutral, which results in a line-to-neutral voltage of 69.
Issue: Are all motors to have a 90 degree phase difference between voltage and current when used with Altistart ATS23?
Product Line: ATS23
Resolution: Must have a .95 lagging power factor--current must lag voltage.
Conext XW+ Series Inverters - W95 Equalize Abort
Unit is faulting during equalization and aborts the equalize process due to dropped transfer, unit displays a W95.
Solar Inverters, XW/SW series
On-Grid & Off-Grid Systems
This unit is faulting because the AC source is lost. This can also occur if the conductors are undersized for distance, creating voltage drop.
This could also happen if you are using a generator that is not correctly size for the system causing the generator to over load.
Wait until AC input (utility grid) returns to in-tolerance condition, if this doesn't happen it may be necessary to lower the AC input voltage lower limit (Advanced Settings>AC Settings). If Generator is undersized try a different source.
PDL 699 has one set of terminals and the PDL 699TB is the twin base model and therefore has a set of terminals for each outlet. The configuration of the switches and sockets
are different as well.
The cover (PDL 691C) for the PDL 691 is only available in White (691CWH), Polished Brass (691MPB), Brushed Bronze (691MBBZ) and Stainless Steel (691MSS). Black is not available.
Yes as of December 2015 the 642MUSB mech can be installed into the extra mech position of the 692X or 695X
This is also available as complete units:
We only do a horizontal single, switched socket with two extra switches - PDL 694XX.
Another alternative would be to use a PDL 691X. This is a vertical single, switched socket with one extra switch.
AC coil replacement for CAD32 and CAD50
Tesys CAD Control Relays
Volt = coil part number
12 = LXD1J7
21 = LXD1Z7
24 = LXD1B7
32 = LXD1C7
36 = LXD1CC7
42 = LXD1D7
48 = LXD1E7
60 = LXD1EE7
100 = LXD1K7
110 = LXD1F7
115 = LXD1FE7
120 = LXD1G7
127 = LXD1FC7
200 = LXD1L7
208 = LXD1LL7
220/230 = LXD1M7
230 595 21 LXD1P7
230/240 = LXD1U7
277 781 30 LXD1W7
380/400 = LXD1Q7
400 = LXD1V7
415 = LXD1N7
440 = LXD1R7
480 = LXD1T7
600 = LXD1X7
690 = LXD1Y7
PDL used to do a complete unit - The 695SP however, this is now obsolete. A Surge Protection Outlet can be made up of parts. You will need to use one of the sockets that have an extra switch space such as the 694X or the 695X and replace the extra switch with our Surge Protection Module, the 600SM.
As of right now, no ION hardware undergoes any testing for seismic and/or vibrational compliance. No meters in the ION family have this compliance. Typical standards are IEEE 693 and IEC 60255-21-3.
Date Created: November 12, 2010
Last Revised: November 18, 2010
Original Author: DD
All content © 1992-2010 Schneider Electric
Legacy KB System (APS) Data: RESL203933 V1.0, Originally authored by LaAd on 11/19/2010, Last Edited by LaAd on 11/19/2010
Related ranges: ION8600, ION75X0 RTU, ION7550/ION7650, ION7300, ION6200
Braking resistor switch on voltage is fixed by hardware and it is not configurable in LXM32.
For LXM32___M2 range threshold is 430 vdc if parameter DCbus_compat = 0 (default) and 395 vdc if parameter DCbus_compat = 1
For LXM32___N4 range threshold is 780 vdc irrespective of parameter DCbus_compat settings.
Master password to reset the ATV11 drives.
Password has them locked out of the drive.
Menu SUP then COD enter master password 696 to unlock the drive.
They both come with a pair of speakers, a plug-in power supply and 10 metres of interconnecting speaker cable.
The 5600BTSA50 50W RMS Bluetooth Amplifier includes a power supply and terminals for connecting a pair of third party speakers.
Below are the pinouts:
Normally Closed (NC) Contact
Normally Open (NO) Contact (recommended connection)
Relay ratings: 1A, 30V AC/DC
Since the user interface allows for either 'normally open' or 'normally closed,' APC recommends using only the normally open contacts and configuring the 'normal' state in the user interface.
What does the OC2P fault mean on the ATV21 and ATV212 drives?
Altivar ATV21 and ATV212
Short circuit or grounding fault during deceleration
The fault means: Short circuit or grounding fault during deceleration
Drop the motor leads and Megger out the motor and cables with a 1KV Megger.
Run drive with no motor connected: Set 605 to 0 and measure voltage coming out of the drive at 20/40/60 hz intervals phase to phase voltage measurement.
Check for proper grounding at the motor and drive.