Frequently Asked Questions
Which remote mechanism can be used with the 41E300PBUD2SM?
Both the 2-wire (41EPBM) and 3-wire (41EPBCLM) remote mechanisms can be used with the 41E300PBUD2SM. There is a difference in the functionality and how they work with the 41E300PBUD2SM.
When connected in a two-way situation with a 3-wire remote mechanism (41EPBCLM) the dimming settings can be changed from either mechanism but these settings will not be retained when turned on from the remote mechanism and will return to full brightness. The 3-wire remote mechanism has an integral LED indicator that can be used.
Using the 2-wire remote mech (41EPBM) will allow the setting of dimming levels from either mechanism and will retain dimming levels previously set when turned on from the remote mechanism. The 41EPBM does not have a LED indicator.