Frequently Asked Questions
Part number comes standard as Vivid White, will need Cool Grey cover to suit.
The part number for the 1 gang Iconic switch , and can the mech be rotated for horizontal or vertical switch plates - 3041VA and yes can be mounted Vertical or Horizontal..
For further information , visit link below:-
Do we have any series ratings with the Masterpact NT and NW breakers?
Masterpact NW, NT
Masterpact breakers in NEMA markets
There are no series ratings for Masterpact NT, NW circuit breakers.
There are none for the obsolete SE or Masterpact MP either.
Transformer lug kits
Applies to Low Voltage Transformers by SquareD/Schneider Electric
Transformers 15 KVA and over may require lug kits
Lug kits can be found in the online Catalog 7400CT0501.
This kit includes 3 lugs per kit
Identifying trip point in a single phase sensitive overload relay
NEMA combination starters
Products sold and used in the United States
Identifying the trip point in a single phase sensitive Tesys D overload relay
The phase loss sensitive overloads are designed to conform to IEC standard 60947-4-1. In that standard is this paragraph:
188.8.131.52.2 Limits of operation of three-pole thermal overload relays
energized on two poles
With reference to table 4:
The overload relay or starter shall be tested in its enclosure if normally fitted. With the relay
energized on three poles, at A times the current setting, tripping shall not occur in less than
2 h, starting from the cold state, at the value of the ambient air temperature stated in table 4.
(Table 4 `A` multiple of current setting states 2 poles at 1.0 times the current setting, the third pole at 0.9)
Moreover, when the value of the current flowing in two poles (in phase loss sensitive relays,
those carrying the higher current) is increased to B times the current setting, and the third
pole de-energized, tripping shall occur in less than 2 h. (Table 4 `B` multiple of current setting is 2 poles
at 1.15 current setting, third pole at 0.0.)
The values shall apply to all combinations of poles.
In the case of thermal overload relays having an adjustable current setting, the characteristics
shall apply both when the relay is carrying the current associated with the maximum setting
and when the relay is carrying the current associated with the minimum setting.