Frequently Asked Questions
You can use a 28902 load break switch with a LV428941 extended rotary handle
Yes - The 28962 suits the INS40 - INS60 load break switches
Does a UV trip or UVR undervoltage release sense phase loss?
Circuit breakers that have a UVR undervoltage trip
The UVR will sense phase loss only on the phase from which its power is taken. The UVR should not be used for a phase failure application, as it can only monitor one phase.