The part number for bracket to suit is 155P.
205mm x 395mm x 155mm (H x W x D) excluding the handle.
Overall depth with standard handle is 213mm.
The dimensions are 121mm (W) X 83mm (H) X 155mm (D).
You can direct mount onto the lid of the 80 or 155mm trunking or use the ISM15150
Other options are the Unistrut 2087016 and adaptors can also be found at cccutting.co.nz
Part number for large mounting flange is 448SD
It is 90mm.
See attached pdf for more information.
The installation sheet for 755FM is available at : https://updates.clipsal.com/ClipsalOnline/Files/Brochures/W0000802.pdf
The installation sheet for 755PFM is available at: https://updates.clipsal.com/ClipsalOnline/Files/Brochures/W0000801.pdf
The part number is 755PFM for photoelectric type and 755FM for Ionisation
Please find attached pdf on these alarms
For further information please visit the Clipsal Web site on the link provided.
The 755FM and 755PFM have a 90mm cut out
For more information on the 755 range of smoke alarms please visit the Clipsal web site on the link provided
Yes there is a secondary power supply it is 9V DC alkaline battery backup
The recess on our 755PFM is 80mm.
Dimensions - 158mm x 158mm x 140mm high.
The 135mm drop in lid would suit the 150mm duct however all drop in products have been obsolete for a at least 2 years.
That bracket will suit the slimline, Saturn, ZEN and OneTouch series plates.
The part code is A9C30211
The Speed-range ratio for Drives is 20:1, 100:1 or 1000:1. This is an indication of how slow the Drive can run the motor, before the motor starts to overheat.
Drive with a 1000:1 ratio is good, as compared to 20:1 or 100:1.
The Altivar 61 and Altivar 71 Range of Drives have the Speed-range ratio of 1000:1 in closed loop and 100:1 in open loop operation.
The speed in RPM (Revolutions per Minute) of a 4 pole, 50 Hz Motor will be 1500 RPM.
If the Drive Speed-range is 1000:1, Drive can run the motor as slow as 1.5 RPM (1500/1000 = 1.5) without overheating.
For 100:1 it is 15rpm and for 20:1 it is 75rpm.
The higher the Speed-range ratio, the slower the motor can be operated safely without overheating.
The 154/2 is the clip to suit any Prestige large format plate 115mm x 115mm
The cut out is 90mm diameter
Yes, there are a couple of options that are bigger than the standard 115mm x 85mm.
There is the P2025/2-WE, M8015LVA-WE or M8025LVA-WE.
The dimensions are 315mm W x 255mm H x 97mm D
The dimensions for part number C2016/2 are:
159mm (L) 47mm (H) 28mm (D)
Hold the test button down for about 10-15 seconds and other smoke alarms on circuit should go off
Yes it complies with AS3786 and also AS/NZS3100
data kit is made of 2 part nos
> PLDSK (which is the Shroud) and then front cover PL125CFCx (x will be the color N,B,W,O) > this is for 125mm duct
> PLDSK (which is the Shroud) and then front cover PL150CFCx (x will be the color N,B,W,O) > this is for 150mm duct
power kit is made of 2 part nos
> PLPSK (which is the Shroud) and then front cover PL125CFCx (x will be the color N,B,W,O) > this is for 125mm duct
> PLPSK (which is the Shroud) and then front cover PL150CFCx (x will be the color N,B,W,O) > this is for 150mm duct
The single cover plate is 118 x 74mm
The double cover which covers two subplates plates is 118mm x 145mm
Board Size: 780mm H x 555mm W x 186mm D
Weight: with Metal Door 21kg, with Glass Door 21.4kg
152 Length x 152 Width x 10 Depth mm
Mounting centre 84mm
A9C30831 is the Acti9 code for the 1P 1NO 32A 230v AC impulse relay.
The dimensions for part number 750MBA are:
145mm (L) x 90mm (W) x 45mm (D)
The Cut-out hole size for a 755PSM flush mount smoke alarm is 90mm.
Some of the key features are:
- Photoelectric technology for faster response to common smouldering fires
- Super low profile, stylish fully recessed design (60% smaller than the average smoke alarm)
- Easy installation and maintenance using a 90mm cut out and clip in/clip out module
- Interconnectable with up to 40 units (compatible with all Clipsal Firetek smoke alarms)
- Built in test/hush function
- 9VDC battery backup (included)
For further information please visit https://www.clipsal.com/Trade/Products/ProductDetail?catno=755PFM
No. Unfortunately, there is currently no base available with wireless interconnect to suit the 755PFM flush series of smoke alarm.
The difference between the Surge Arrester references 15597 and 16447 is as follows:
1.) 15597 is a PF20 3Pole Fixed type Type 2 LV Surge Arrester.
2.) 16447 is a PRD20 3Pole Withdrawable type Type 2 LV Surge Arrester.
Both are suitable to be used in low risk level and for use in TNC Earthing systems.
The difference is that 15597 at its end of life needs to be replaced as it is Fixed type, while 16447 at its end of life can be reused by simply replacing the cartridge as it is Withdrawable type, and the other major advantage is that the wiring does not get disturbed.
Unfortunately we do not have a mounting block to suit 31/3VX, large format blank switch plate.
Will the 9001KA contact blocks work at 24VDC?
9001 KA1-KA6, KA21-25, KA31-35, KA1G-KA6 contact blocks will work on 24VDC providing the do not exceed 1.1amp make and break nor exceed 10 amps continuous current.
CTA-ID : 15554
Please see attached document and drawing.