Frequently Asked Questions
K rated Transformers
Applies to Low Voltage Transformers by SquareD/Schneider Electric
K rated Transformers for application on Non Linear loads
The Transformer industry does not typically use a `K1` rating. Rather it is a non-recognized term that some (consultants, OEMs, contractors) use to denote a Transformer that will only be feeding Linear loads such as motors, compressors, solenoids, heaters, etc. In other words, K1 refers to a Transformer that does not have a `K` rating such as K4, K9, K13, K20.