The below list are all measured in mm - all Reed Switches are Normally Closed with the magnet in place (NC)
5460 18h x 19w x 13d
5460HD 88h x 38w x 10d (cable lenght: 280)
5460RF 78h x 73w x 27d
What would cause the assembly 106 and 107 I/0 tables in somove to reset to default after closing out somove and or power cycling the ATV930 drive?
Somove and ATV930
assemblies 106 and 107 are not supported
Assemblies 106 and 107 are only supported in Somove and not the Drive so the drive will not retain the settings and will reset back to default after power cycle or if you open up somove again and copy from drive to PC.
Reading modbus register from Digitrip 810D using register list
Modbus register list for Digitrip 810D is attached below.
The alarm status's are stored in registers 5771-5778 with each alarm set to a bit indexed from zero. For example, if one needed to determine if the over current alarm for phase A was active you would read register 5771 and look to bit zero. If the register reading program is not capable of displaying binary (bit level) information, the information may be entered into the Windows calculator and converted from decimal to binary.
Alarm No. Alarm Description
01 Over Current Phase A
02 Over Current Phase B
03 Over Current Phase C
04 Over Current Neutral
05 Over Current Ground
06 Under Current Phase A
07 Under Current Phase B
08 Under Current Phase C
09 Current Unbalance Phase A
10 Current Unbalance Phase B
11 Current Unbalance Phase C
12 Phase Loss, Current
13 Over Voltage Phase A
14 Over Voltage Phase B
15 Over Voltage Phase C
16 Over Voltage Phase A-B
17 Over Voltage Phase B-C
18 Over Voltage Phase C-A
19 Under Voltage Phase A
20 Under Voltage Phase B
21 Under Voltage Phase C
22 Under Voltage Phase A-B
23 Under Voltage Phase B-C
24 Under Voltage Phase C-A
25 Voltage Unbalance A
26 Voltage Unbalance B
27 Voltage Unbalance C
28 Voltage Unbalance A-B
29 Voltage Unbalance B-C
30 Voltage Unbalance C-A
31 Voltage Loss (Loss of A, B, or C, but not all)
32 Over kVA 3-Phase Total
33 Over KW Into the Load 3-Phase Total
34 Over KW Out of the Load 3-Phase Total
35 Over kVAR Into the Load 3-Phase Total
36 Over kVAR Out of the Load 3-Phase Total
37 Over Current Demand Phase A
38 Over Current Demand Phase B
39 Over Current Demand Phase C
40 Over Current Demand 3-phase Total
41 Over Frequency
42 Under Frequency
43 Lagging True Power Factor
44 Leading True Power Factor
45 Lagging Displacement Power Factor
46 Leading Displacement Power Factor
47 Suspended Sag/Swell
49 Over Value THD Current Phase A
50 Over Value THD Current Phase B
51 Over Value THD Current Phase C
52 Over Value THD Voltage Phase A-N
53 Over Value THD Voltage Phase B-N
54 Over Value THD Voltage Phase C-N
55 Over Value THD Voltage Phase A-B
56 Over Value THD Voltage Phase B-C
57 Over Value THD Voltage Phase C-A
58 Over K-Factor Phase A 1071 Tenths % A
59 Over K-Factor Phase B 1072 Tenths % A
60 Over K-Factor Phase C
61 Over Predicted kVA Demand
62 Over Predicted KW Demand
63 Over Predicted kVAR Demand
64 Over kVA Demand Level 1
65 Over kVA Demand Level 2
66 Over kVA Demand Level 3
67 Over kW Demand Level 1
68 Over KW Demand Level 2
69 Over KW Demand Level 3
70 Over kVAR Demand
71 Over Lagging 3-phase Avg. Power Factor
72 Under 3-Phase Total Real Power
73 Over Reverse 3-Phase Power
74 Phase Reversal
75 Status Input 1 Transition from Off to On
76 Status Input 2 Transition from Off to On
77 Status Input 3 Transition from Off to On
78 Status Input 4 Transition from Off to On
79 Status Input 5 Transition from Off to On
80 Status Input 6 Transition from Off to On
81 Status Input 7 Transition from Off to On
82 Status Input 8 Transition from Off to On
83 Status Input 1 Transition from On to Off
84 Status Input 2 Transition from On to Off
85 Status Input 3 Transition from On to Off
86 Status Input 4 Transition from On to Off
87 Status Input 5 Transition from On to Off
88 Status Input 6 Transition from On to Off
89 Status Input 7 Transition from On to Off
90 Status Input 8 Transition from On to Off
99 End of Incremental Energy Interval
101 End of Demand Interval
102 End of Update Cycle
103 Over Analog Input Channel 1
104 Over Analog Input Channel 2
105 Over Analog Input Channel 3
106 Over Analog Input Channel 4
107 Under Analog Input Channel 1
108 Under Analog Input Channel 2
109 Under Analog Input Channel 3
110 Under Analog Input Channel 4
201 Voltage Swell A-N/A-B
202 Voltage Swell B-N
203 Voltage Swell C-N/C-B
204 Current Swell Phase A
205 Current Swell Phase B
206 Current Swell Phase C
207 Current Swell Neutral
208 Voltage Sag A-N/A-B
209 Voltage Sag B-N
210 Voltage Sag C-N/C-B
211 Current Sag Phase A
212 Current Sag Phase B
213 Current Sag Phase C
214 Current Sag Neutral
Legacy KB System (APS) Data: RESL209554 V1.0, Originally authored by MaTh on 11/02/2012, Last Edited by MaTh on 11/02/2012
Related ranges: CM2000 series
Dimensions are 190w x 206h x 102d
ATV630 Process drive with Ethernet IP option card how do you set it up to use assemblies 103 and 104?
Altivar ATV630 ATV650 ATV660 etc
They needs to set up the ATV630 drive with the optional Ethernet IP card to use assemblies 103 and 104.
The ATV630 Ethernet IP card VW3A3720 does not support assemblies 103 and 104. You will have to configure your PLC's Ethernet Scanner module for assemblies 100 and 101.
Board Size - 376w x 392h x 100d Hole Size - 335w x 357h x 80d inc wallboard
This is a 30 module board flush mounting style which comes in white only.
This also replaces the 4FCC24 and 4FCC36.
Please see following link and look under the documents tab for more information and complete range of products.
Dimensions 272w x 206h x 102d Please note this product has been obsoleted
No, 10 kA Potentiometer for the XACA range.
The part number for a 108 pole Chassis for iC60C/B's for the MB switchboards is - C3251083
No unfortunately this part is not available.
No it is not. Twido PLC software will only be compatible with Windows 7.
User needs to know which I/O units are compatible with VAMP 221
The following I/O units are compatible with VAMP 221. Details for each unit are provided below.
- VAM 12L accommodates up 10 arc APS_SENSORS, 3 APS_SENSORS have dedicated trip outputs
- VAM 12LD accommodates up 10 arc APS_SENSORS, 3 APS_SENSORS have dedicated trip outputs
- VAM 10L accommodates up 10 arc APS_SENSORS
- VAM 10LD accommodates up 10 arc APS_SENSORS
- VAM 3L accommodates up to 3 fiber loops
- VAM 3LX accommodates up to 3 fiber loops with sensitivity adjustment
- VAM 4C accommodates up to 3 current transformers
- VAM 4CD accommodates up to 3 current transformers
No, XBTL1000 does not support Windows 10. It is suggested to use a Virtual Machine running Windows xP or Windows 7 if you only have a Windows 10 PC.
Modsoft error 109 ""PLC returned undefined exception" when trying to go online to the PLC is usually caused by the PLC being in "Kernel" mode (Run light flashing). Cycle power on the PLC and if the Run light still flashes, download the executive firmware to see if you can get the Run light to stop flashing.
The alarm log is a circular buffer. It means that, once it filled up, new alarm events will overwrite the oldest alarm events. For example, if your alarm log size is set to 100 records, it will work like this:
- events 1 to 100 will fill up the alarm log.
- event 101 will overwrite event 1.
- event 102 will overwrite event 2.
- event 199 will overwrite event 99.
- event 200 will overwrite event 100.
- event 201 will overwrite event 101.
Legacy KB System (APS) Data: RESL183431 V1.0, Originally authored by MiMe on 04/10/2007, Last Edited by MiMe on 04/10/2007
Related ranges: Vijeo Designer
The Twido relay outputs are rated for:
- 2A/ 240 VAC or 2A/ 30 VDC (with 1800 operations/hour max) :
- electrical life : minimum 100 000 operations
- mechanical life : minimum 20 x 106 operations
Legacy KB System (APS) Data: RESL172642 V1.0, Originally authored by on , Last Edited by on
Related ranges: Twido
The power consumption of a SILC LED (CLSK12WF, CLSK12CF) is 10W when at full brightness
Can Vijeo Designer Lite run on Windows 10?
Vijeo Designer Lite V1.3
No, Vijeo Designer Lite V1.3 does not support Windows 10. Please install Vijeo Designer Lite on a Windows 7 OS or older.
DBF15 D Board Flush 15 Way 1.7Kgs
Board size 376w x 258h x 100d
Hole size335w x 223h x 80d inc wallboard
Board Size - 286w x 258h x 100d
Hole Size - 246w x 223h x 80d inc wallboard
335w x 631h x 80d inc wallboard
This is different to the old DBF45 which stated 491mm High.
SoMachine V4.1 SP2 windows compatibility
SoMachine V4.1 SP2 only supports Windows 7, 32 and 64 bit, as well as Windows 8.1, 32 and 64 bits.
SoMachine V4.2 supports it.
Digitrip RMS 810D
Legacy KB System (APS) Data: RESL205052 V1.0, Originally authored by MaTh on 04/11/2011, Last Edited by MaTh on 04/11/2011
Related ranges: Digitrip DS 810D
After connecting a VAMP 10L (VAM10LSE) module to a VAMP 321 the error light is illuminated.
VAMP ARC Flash Modules
The VAMP module must be configured to talk to the VAMP 321. Until this communication connection is established the VAMP 10L module will be in an error status. (This is also for any other ARC Flash Module)
Connect to the VAMP 321 using the VAMPset software. Navigate to the ARC Protection screen, then click on the Install arc sensors and I/O units > select install, then write the changes to the VAMP 321. The VAMP 321 will locate all I/O devices along with any connected sensors.
After connecting a VAMP 10L module to the VAMP 321 relay the VAMP 321 arc flash sensors no longer triggers a trip.
This issue may be caused by connecting the VAMP 10L module to the VAMP 321 incorrectly.
Verify that the communication port on the VAMP 321 matches that on the VAMP 10L. If they do not match correct this then reconfigure the connection under the ARC Protection screen within VAMPset and write these changes to the VAMP 321. Finally confirm functionality.
Ten in a box (clipsal page 104 - 2014 Pocket Book)
The replacement for the MSW110-TW two-way 10A weather proof switch is a 56SW110/2.
Some of the key features are:
- 1 gang
- Four-terminal switch
- 107 mm Height x 101 mm Width x 83 mm Depth
- 8 mm hole diameter
- 1.5 - 6 sq mm conductor terminal
- M80 Motor rating
For further information please visit https://www.clipsal.com/Trade/Products/ProductDetail?catno=56SW110/2
Standard Active Silver Caps are not able to be purchased on their own. The only caps available for the range is the labelled cap pack which also comes with 10x blank Cat's Eye Caps. The part number for the Cap pack is 60PBC-3A.
Use a PDL654PBM - Push Button Universal Dimmer Module.
This has a minimum load of 10W
10A 3 position, Labelled Low-Off-High = 39M
10A 3 position, Labelled Auto-Off-Man = 38MAOM
10A 3 position, Labelled Sensor-Off-On = 39MSON
The closest junction box we would have is a 265/3. The dimensions of that junction box is 108mm(H) X 108mm(W) X 76mm(D).
- Surface mount
- Dimension: 108 mm Length x 108 mm Width x 76 mm Height
- 89 mm screw centres C, 89 mm screw centres D
- Weatherproof, full cover plate
For further information please visit www.clipsal.com/Trade/Products/ProductDetail?catno=265/3
Shop tests, unloaded motor
Testing the ATS with an unloaded motor, usually trips the ATS22 with SSCr.
After entering the correct motor data, and set the LAC to ON:
- t90 = Factory 30 but changed to 10. ( Due to No Load connected and monitor ramp acceleration. This value to be changed back or increased when in the field under actual start-up. )
- ILt = Factor 350 changed to 200% for Shop Testing. Value to be changed in the field if Current Limit trips out.
- tLS = Factory 15s changed to 60s for Shop Testing. ( Changed back to 15s after completion of testing. )
- ACC = Factory 10s change to 60s for Shop Testing. ( Changed back to 10s after completion of testing. )
- SSC = Factory On, changed to oFF. ( Using Voltage control vs. Torque. )
- ItH = Found to be on ErUn, changed to On. ( Factory is On. )
No. TwidoSuite, Twido is an obsolete product and has been replaced with the M221 and SoMachine Basic software that will run on Windows 10. The last version of TwidoSuite is version 2.31.4 and it will run on Windows 7 64 bit. With the SoMachine Basic and M221 you can import the old Twido programs into SoMachine Basic and load program into the M221.
Board Size - 376w x 392h x 100d Hole Size - 335w x 357h x 80d inc wallboard
Board Size - 376w x 392h x 115d Hole Size - N/A.
Board Size - 376w x 666h x 100d Hole Size - 335w x 631h x 80d inc wallboard
Board Size - 376w x 666h x 115d Hole Size - N/A
Board Size - 376w x 800h x 100d Hole size - 335w x 765h x 80d inc wallboard
Board Size - 376w x 800h x 115d Hole size - N/A
If it is to be used in a motor protection then the RM4TA02 or 32 should be used
The 02 has a fixed 0.5s delay, the 32 has an adjustable 0.1 - 10s delay
See attached data sheets.
Fiber Pod Extender Signal Quality Variance
NetBotz Fiber pod extender NBAC0212
NetBotz can still communicate with pods even with some signal loss.
The NetBotz Fiber Pod Extenders will function properly with up to 10dB level of signal loss between the local and remote units of the extender.