21 June 2021
The LUCA12BL is to be controlled directly with the output of a PLC.Product Line:
Tesys U lineEnvironment:
PLC doing remote control of the motor starter.Resolution:
Yes, if the output of the PLC is 24 V DC and can handle an inrush of 220mA . A reversing module will add 120mA to the inrush when it has to change the direction of the motor.