Frequently Asked Questions
Function of a GAVD0110 auxiliary contact.
Tesys GV manual starters
Contacts do not appear to be working properly.
The GVAD** can only be installed on left side of product and the GV2 must be in OFF position when mounting.
The GVAD0110 has 2 different contacts
One is fault signaling contact (terminals 95/96) NC contact and the second is only standard auxiliary NO contact (terminals 53/54 ).
Fault signaling defect contact should be always in close position excepted when there is fault on GV2 ( short circuit or overload ) at this time contact open.
This fault signaling defect contact is not related to ON/OFF position of GV2’s but to reset back to NC the device must be switched back to the ON position.
Auxiliary contact report the ON/OFF position of GV2’s.
This Auxiliary NO contact is on Open when GV2 is on OFF position and close when GV2 is ON position.
GS2AH handle or knob mounting directly to a GS1DDU3?
Operating Mechanisms and Disconnect Switches
Wants the handle or knob (GS2AH110 etc..) be mounted directly to GS1DDU3.
No, but they can used an internal handle kit - Part number GS1AD010