Frequently Asked Questions
Checking on the DC current contact ratings for the CAD50, CAD32, CAD503, CAD323, CAD506, and CAD326 relay.
CAD Industrial Relays
Relays and Timers
125V DC - 0.55 Amps make and break, 2.5 Amps cont.
250V DC - 0.27 Amps make and break, 2.5 amps cont.
600V DC - 0.10 Amps make and break, 2.5 Amps cont.
Identifying power terminal lug data for the D2 style contactors
IEC Contactors and Starters
Tesys D line contactors
Power terminal lug data required
For contactors with screw clamp terminals:
stranded cable w/o cable end : One #10-3 AWG or Two #10-4 AWG per terminal.
stranded cable w/cable end: One #10-4 AWG or Two #12-2 AWG per terminal.
solid cable: One #10-3 AWG or Two #10-6 AWG per terminal.
What is the hot and neutral on the coil terminals for CAD50BL?
Tesys D IEC Style Relays
Determine if relay will work for a specific application.
Yes, the DC coil is polarity sensitive - A1 is positive and A2 is negative.
Safety category listing of CAD TeSys relays
TeSys D Relays
The Tesys CAD32** and the CAD50** relays and top mounted adder decks have positively guided or linked contacts. Therefore the contacts meet IEC EN60947-5-1 and are approved to use in safety systems through category 4.