Frequently Asked Questions
Can we recommend using the Acti9 iCT contactor range as an emergency stop contactor?
Acti9 iCT contactors (ex:A9C2083) are only certified according to IEC 61095 Std for household and similar purposes.
They are not compliant according to IEC 60947-4-1 Std and we can not recommend to use in emergency stop function as they are not suitable for isolation in OFF position, nor in motor starting application.
For this kind of application we can recommend to use dedicated Motor Management solutions of TeSys range.