17 May 2022
The secondary fuse of the control transformer is blowing.
All enclosed drives
All models and serial numbers
Caused by short circuit to ground. Possible loose wire or defective or damaged contactor coil.
Trace short circuit with ohm meter. Replace coil if necessary.