Part no for mounting block is 447
This customer support bulletin identifies a potential issue with ION Enterprise 5.6 B447 and 448 when upgrading to Service Pack 2, and explains the resolution.
There is a problem with the ION E 5.6 SP2 Installer when executed against builds 447 and 448 of ION Enterprise 5.6. The problem results in an upgrade installation failure when run on a client machine, secondary server or database server. The upgrade of a primary server will succeed When the SP2 install fails, the customer is left with the pre-existing version (5.6 or 5.6 SP1). This rollback will not appear to impact the function of the client, secondary or database server, but will leave the customer with a system where the primary is using a different version than the other machines; an unsupported configuration which may result in data and connection errors. We have determined that the stated builds were delivered during May, June and July 2007. The issue does not affect build 449, which has been in release since July 31st, 2007.
A modified version of the service pack will be available for download from the website by October 13th, 2008, at 12:00 PM GMT. Any installation of Service Pack 2, whether by the customer or a proxy on behalf of the customer, must use the modified version. The modified version will work with build 449 as well.
The following workaround is available for customers unable to wait for the modified version of the service pack. However, as the workaround involves shipment and end-customer delivery of a CD, it is likely that downloadable service pack will be available by the time the workaround can be implemented. In addition, there are steps which should be taken in the event the customer needs to upgrade a database server, and we strongly suggest tech support be contacted if this is the case.
- Verify the customer is using build 447 or 448 of ION Enterpise 5.6, as the following is not necessary if they are using build 449. To verify, open the file "ION Enterprise5.6Setup.log" on the client, secondary or database server. Note: If you have previously installed Service Pack 1, open the file called "ION Enterprise_5.6_SetupLog(1).log" instead. The build will be listed on the 15th line, and will resemble "OK (0) ION Enterprise 5.6 build 448".
- Request a new ION Enterprise 5.6 CD via PMC Technical Support. All new versions use build 449.
- Upon delivery, uninstall ION Enterprise 5.6.
- Re-Install using the delivered CD.
- Install Service Pack 2. At this point, the version of the service pack is not of consequence, as there is no issue with build 449.
If you have questions about this bulletin, use any of the various means of contacting us presented on the following web page to communicate to us:
Last Revised: 22 Sept 2008
All content © 1992-2008 Schneider Electric
Legacy KB System (APS) Data: RESL192820 V2.0, Originally authored by DaMi on 09/24/2008, Last Edited by DaTh on 10/29/2008
Related ranges: ION Enterprise V5.6
No longer available, we only have PDL 647
No. This product is only available in white.
Smith Elements & Controls - 0800 437 638
No - It can only be mounted vertically
Levco are the suppliers of Hospitality cards +64 9 444 0161
The card is not supplied in the PDL626N pack.
Not available, need to use PDL 647
The PME 8.2 Power Quality offers the option to use the SEMI F47 curve. If this is used, you will notice that the curve is incorrect.
The SEMI F47 standard allows a 50% voltage sag for up to 0.2 seconds. The curve incorrectly uses 0.02 seconds, rather than 0.2 seconds as the tolerance for a 50% sag.
Power Monitoring Expert 8.2
Using the PQ Report with the SEMI F47 curve.
The definition of the SEMI F47 in PME 8.2 is incorrect.
*Warning: Irreparable database damage can occur. This procedure should only be performed by users familiar with SQL Server Management Studio. Databases should be backed up prior to performing this procedure.*
Log into SQL Server Management Studio and run the attached SQL script (PME8.2_SEMIF47_CurveUpdate.sql) to correct the curve definition. See attached document
This problem has been addressed in PME 9.0
Issue: Will the Altivar ATV18 drive perform inverse PI?
Product Line: ATV18
Resolution: No, you will need to provide an inverse transducer.
This is not a removable mech products its a soild units
If mounted on its side the products is still complant when mounted
My Network Management Card (NMC) is losing SNMPv3 connectivity after a certain amount of time but other communication protocols (web, FTP, SSH, Telnet, SNMPv1, etc) continue to work properly.
- Network Management Card 1 (NMC1) - AP9617, AP9618, AP9619
Devices with an embedded Network Management Card 1 include (but are not limited to): Metered/Switched Rack PDUs (AP78XX, AP79XX), Rack Automatic Transfer Switches (AP77XX, Environmental Monitoring Units (AP9320, AP9340, NetBotz 200)
- Network Management Card 2 (NMC2) - AP9630/AP9630CH, AP9631/AP9631CH, AP9635/AP9635CH
Devices with an embedded Network Management Card 2 include (but are not limited to): 2G Metered/Switched Rack PDUs (AP86XX, AP88XX, AP89XX), Certain Audio/Video Network Management Enabled products.
- All serial numbers
- Any device listed above utilizing SNMPv3
- NMC1 AOS v3.7.0 and below; NMC2 AOS v5.0.X and below
- NMC1 AOS v3.7.3 and higher
An issue has been identified with the SNMPv3 task on Network Management Card 1 and 2 based devices. SNMPv3 communication will be lost after approximately 49 days and 17 hours. The NMC will continue to run normally, with the exception of the SNMP process, which will not run.
Update (July, 2016): Specific to NMC1 products, this issue had previously been fixed for AOS 3.7.3 and higher. The maximum SNMPv3 uptime allowed was modfied from 49.7 days to 497 days. At the 497 uptime day mark, assuming the management uptime had reached this point, the Network Management Card interface would have had to be rebooted though the web, CLI, or SNMPv1 interfaces in order to regain SNMPv3 communication. NMC2 AOS v5.1.X also contained a fix to avoid an SNMPv3 communication loss completely.
With NMC1 AOS v3.9.2 and higher, this issue has been fully resolved and the 497 uptime limitation has been lifted and SNMPv3 communication through StruxureWare Data Center Expert or any third party SNMPv3 NMS will not be affected after 497 days of uptime. This AOS (or newer) will be released for different firmware applications in the coming months which are available at https://www.apc.com/tt/en/tools/download/. Certain applications are available immediately, such as Rack PDU.
Issue: Are the Altistart ATS23 units repairable?
Product Line: ATS23
Resolution: No. These are no longer repairable. Replace with a current softstarter
This article contains the Material Safety Data Sheet for R407C Refrigerant.
Data Center Cooling.
The input voltage selector must be adjusted in order to accommodate the new voltage requirement. This process is outlined on page 10 of the owner's manual
Needs the replacement contacts or interior for 9001BW pendant stations
9001BW Pendant control
North American Products
Note replace the * with the enclosure color Y = yellow, B = black R = red
9001BW92* - replacement interior is 9001BOC368
9001BW93* - replacement interior is 9001BOC368
9001BW94* - replacement interior is 9001BOC358
9001BW95* - replacement interior is 9001BOC359
9001BW96* - replacement interior is 9001BOC358
9001BW97* - replacement interior is 9001BOC359
9001BW98* - replacement interior is not available
9001BW90*U - replacement interior is 9001BOC366
9001BW91*U - replacement interior is 9001BOC359
9001BW94*U - replacement interior is 9001BOC358
9001BW100*U - replacement interior is 9001BOC367
9001BW102*U - replacement interior is 9001BOC367
No, unfortunately this mounting block is unavailable in black. As an alternative we can do the 448SD Mounting block in black however it has a depth of 14mm a pose to 28mm.
Some of the key features are:
- Large size format, deep mounting
- With metal inserts, 16 mounting screw positions
- Various colours available
For further information please visit www.clipsal.com/Trade/Products/ProductDetail?catno=448SD
The Concept Application Loader (372 SPU 477 01 V26. ) does allow the importing of .ASC files through the Concept Converter. It also allows the user to open a .prz (archived) project. The execloader is also included.
Legacy KB System (APS) Data: RESL168357 V1.0, Originally authored by on , Last Edited by on
Related ranges: Concept
The 448 should be used with a large plate Prestige switch.
The Acti 9 Breakers can work up to 440 VAC as per typical data sheet
The part number is PDL679CWH.
Yes, we do have a deeper version of the 448SD, large format, mounting block. The part number is 448.
The depth of the 448SD is 14mm where as the 448 has a depth of 28mm.
The Concept Application Loader (372 SPU 477 01 V26. ) is a simple tool to download Concept 2.6 Projects. It is a stripped down version of Concept with no on-line editing capability, no saving of an application, no changes to the configuration, and no viewing of the application code. The Reference Data Editor will be available. For projects that are protected the reference data editor will be available in read only mode.
Legacy KB System (APS) Data: RESL163987 V1.0, Originally authored by on , Last Edited by on
Related ranges: Concept
The C-Bus Spectrum touchscreen has a 4.7 inch display (119mm)
It uses a LCD 320 x 240 pixel screen with a colour range of up to 65,536 colours
It has a viewing angle of 60 degrees left and right, 70 degrees up and 40 degrees down.
The durability of the screen advertises up to 1 million presses
Power loss of our RFI filter VW3A58407 and VW3A58408.
This information is not available for the moment.
401 = 5 w
402 = 11 w
403 = 11 w
No information for 407 and 408.
Legacy KB System (APS) Data: RESL156483 V3.0, Originally authored by on , Last Edited by on
Related ranges: Altivar 58
AC coil replacement for CAD32 and CAD50
Tesys CAD Control Relays
Volt = coil part number
12 = LXD1J7
21 = LXD1Z7
24 = LXD1B7
32 = LXD1C7
36 = LXD1CC7
42 = LXD1D7
48 = LXD1E7
60 = LXD1EE7
100 = LXD1K7
110 = LXD1F7
115 = LXD1FE7
120 = LXD1G7
127 = LXD1FC7
200 = LXD1L7
208 = LXD1LL7
220/230 = LXD1M7
230 595 21 LXD1P7
230/240 = LXD1U7
277 781 30 LXD1W7
380/400 = LXD1Q7
400 = LXD1V7
415 = LXD1N7
440 = LXD1R7
480 = LXD1T7
600 = LXD1X7
690 = LXD1Y7
LV429210 - Is Vigi block MH type for NSX100/160 (200 to 440 V)
LV431535 - Is Vigi block MH type for NSX250 (200 to 440 V)
Even though Tech datasheet specifies the LV429210 is rated for NSX upto 250, It is recommeded to use the VIgi module only for NSX 100/160.
However, LV431535 can be used for NSX100/160/250.
The maximum length of a Modbus Plus network cable without repeater is 457 metres (1500 ft).
Contact Rating of 9013F Pressure Switches
Pressure, vacuum and Float Switches
9013 Type F Pressure Switch
Those contacts have a control circuit rating of A600.
They are DC rated at 1/4 HP at 115V and 230V (Except form M4)
They are Single Phase AC rated 1 1/2 HP at 115V, 2 HP at 230V
They are Polyphase rated 2 HP at 115V, 3 HP at 230V, and 1 HP at 460/575V.
This also applies to the 9013 FHG2, 9, 12, 13, 44, 49 9013 FSG, and FSW.
Most end users choose to use the ABE7 CPA412 Telefast blocks with the BMXART0814 module because the CJC compensation is done automatically. However in some cases the
end user may choose to use an external pT 100 RTD rather than the Telefast block. If you choose to add the pt 100 externally it would be wired as follows.
The pT100 would be wired to Channel 4, EX+ and EX- terminals
In the Module configuration screen select the following
Temperature from Ch 4-7 bloc
Testing XW AGS auto-start function
By setting the 30 second start voltage higher than the actual battery voltage, the auto-start function can be tested
as long as no grid voltage is passing thru AC1, otherwise the AGS will not be called upon to start.
Temporarily disable charge controllers to allow the battery voltage to rest. Make sure no sensitive electronics
are needed during this time because they may see the grid interruption and reset.
Make sure to set the 30 sec start voltage back down to a reasonable level after
test is completed. LBCO must be set lower than 30 sec start voltage.
Recommended settings :
30 second start V : 46.5 (23.5 for 24V model)
LBCO : 44V (22V for 24V model)
All other start/stop parameters should be disabled.
Multi 9 (M9) breaker and 480V breakers
Applies to Multi 9 (M9) circuit breakers
Need a 480V breaker in the miniature style.
No, the Multi 9 breakers are not rated 480V delta.
The UL 1077 listed M9 is rated for 480Y/277, not 480V delta.
The IEC version has a 440Vac rating
The UL 489 version has a 480Y/277vac rating (.5A-20A), 240 volts (.5 -35A).
For additional information on the ratings please see systems catalog in download center.
Reason for substitution: end of life
Substitution date: 30/12/2009
This product is replaced by:
LC1D40AN7 - TeSys D contactor - 3P(3 NO) - AC-3 - <= 440 V 40 A - 415 V AC 50/60 Hz coil
ISX Manager 4.6.1 (or any lower version) does not support Windows Vista for the following reasons:
When accessing the ISX Manager for the first time from a client, a local client based on Java is installed onto the local machine.
This client was not designed for Windows Vista. Due to significant changes in Windows Vista and its implementation of Java, the client will not work on Windows Vista.
Affected products: all current ISX Manager versions including 4.6.1.
ISX Manager version 4.7 fully supports Vista.
The part number for a 6 hole active link that can fit a 25sqmm cable is L6/25R
Some of the key features are:
- 6 hole
- 2 tunnel- 7.5 mm diameter
- 1 tunnel- 5.5 mm diameter
- 3 tunnel- 4.7 mm diameter
- Dimensions: 65 x 46 x 43 mm
For further information please visit https://www.clipsal.com/Trade/Products/ProductDetail?catno=L6/25R
- Enable the Push Project Editor within the Windows Firewall rules for all network types
- Note: turning off the firewall in this instance will not allow the traffic through
Socket connection dropped:
The socket connection to the controller can be re-established by going into properties of a controller, selecting ‘Get Settings from PC4’.
If you are still not able to upload to the controller please contact Level 2 Technical Support on 1300 722 247
Yes, the form factor of the new unit is exactly the same as the previous generation C-Touch Colour.
The Wall Box, Nail Bracket and Gyprock Bracket do not need to change.
For further Technical Support Please call 1300 722 247
User wants to know what port the Com'X uses to upload data to cloud services Remote Service Platform (RSP)
Com'X uses port 443 with SSL to upload data to RSP.
"If you double-click on a managed device within InfraStruXure Manager and receive the error below then please follow the steps outlined to correct the issue.
InfraStruXure Manager encountered an error attempting to connect to the device. Error Code 407, Hex: 00000197.
This error is caused by not configuring the Proxy settings within the InfraStruXure (ISX) Manager. Verify that the ""Proxy Enabled"" box is checked and that the correct ""Host"" and ""Port Number"" have been entered. Make sure that the Username and Password for the proxy is setup correctly in ISX Manager. The proxy settings are set under the ""System Management-->Network--->Proxy Settings"" menu.
Finally, make sure that the proxy server allows connection from the network segment where ISX Manager and the APC devices are installed. The proxy settings are set under the ""System Management-->Network--->Proxy Settings"" menu.
Clarify the dimension of ION 8650 meter switchboard (285 x 228 x 163) on page-4 under mechanical characteristics of ION8650 datasheet. The (285 x 228 x 163) dimensions are not mentioned on page-8 of ION8650 datasheet.
The datasheet showing the meter dimensions is misleading
The correct dimensions are like those in the mechanical drawing: 226 mm high x 147 mm wide x 189 mm deep. The required cut-out will be, as on page 3, 149 mm wide x 230 mm tall.
Note: the mounting bolts are size 10-32.
DC under-voltage shutdown (immediate) occurs if DC voltage is below 16 VDC (24 V system) or 32 VDC (48 V system).
XW Series Inverter Charger
Check for the correct battery voltage at the inverter's DC input terminals. Check for an external DC load on the batteries. Check condition of batteries and recharge if possible.
The fault clears and the inverter restarts when DC voltage reaches VLBCO+2 V (24 V system) and VLBCO+4 V (48 V system).
Looking for the vibration and shock specification for the HMIGTU series.
HMIG5U, HMIG3U, HMIDT351, HMIDT542, HMIDT551, HMIDT642, HMIDT643, HMIDT732
IEC/EN 61131-2 compliant
5...9 Hz Single amplitude 3.5 mm (0.14 in.)
9...150 Hz Fixed acceleration: 9.8 m/s2, X, Y, Z directions for 10 cycles (approx. 100 min.)
IEC/EN 61131-2 compliant
147 m/s2, X, Y, Z directions for 3 times
LC1K0910N7 replaces LC1K0910Q7 Contactor.
The coil is rated @ 415V AC but can operate at plus or minus 10% of coil votlage.ie Between 373.5V AC AND 456.5V AC
TeSys K contactor - 3P(3 NO) - AC-3 - <= 440 V 9 A - 400...415 V AC coil
For more information see;