System words 160 through 167 (%SW160 - %SW167) provide health status of M340 racks 0 through 7. 0 indicates an IO fault. 1 indicates correct operation of the IO module.
Unfortunately we do not have a mounting block to suit 31/3VX, large format blank switch plate.
Unfortunately not, we do not have a replacement for 4RCBE116/30Q Quicklag 16A RCBO.
Yes, it is rated up to 16A
It means 20A incandesent, 16A fluro
The part number for a Schneider, 60 pole, indoor DB with 160 amp main switch is an MB260E31.
Use a PDL654PBM - Push Button Universal Dimmer Module.
This has a minimum load of 10W
User name and password lengths for InfraStruXure Central and Netbotz appliances for an SNMP version 3 inform.
Netbotz SNMP v3
SNMP version 3 requirements
v3 informs only work under certain circumstances.
md5/des user/password must be 8-15 characters
md5/aes user/password must be 8-15 characters
sh1/aes user/password must be 16+ characters
sh1/des user/password must be 16+ characters
for md5 the user name and password only work if they are between 8-15 characters.
for sh1 the user name and password only work if they are >16 characters.
It means the relay module can switch a load of up to 16A resistive or a 6A fluorescent load.
Yes, it is a PDL 600RM with a 16A resistive rating
It means it has a 16A fluro rating
Unity Pro XL V6.0 introduced MBP_MSTR FC 16. This function code allows the user to change the log in status of an ethernet port. In cases where you are unable to connect to a Quantum PLC because the ethernet port is seen as " Already logged in" this FC will prove useful. MBP_MSTR FC 16 will allow you to change the port status to "logged off" and allow the Unity user to log in.
This would be preferable to using FC 10 (Reset Option module) or performing a power cycle of the PLC.
There are minimum requirements that the user must meet in order to use MBP_MSTR FC 16. 140NOE77101 minimum firmware version....4.9
140NOE77111 minimum firmware version....5.0
140CPU65x xx minimum copro firmware version 3.5
Legacy KB System (APS) Data: RESL207500 V1.0, Originally authored by DaSo on 02/24/2012, Last Edited by DaSo on 02/24/2012
Related ranges: Unity Pro - SoCollaborative software
The part number for the 48 Poles IP42 Metal Distribution Board with 160 Amps Main Switch is "MB248D31"
What is the maximum cable distance from an ATV312 drive to the motor?
ATV312, Altivar 312, ATV320, Altivar 320
The ATV312 shows that an output filter or choke is required for any cable distance between the drive and motor exceeding 164 feet (50 meters). Above 164 feet, there is a change with shielded vs non-shielded.
From 164 feet to 330 feet (100 meters) you can use the LR filter cell or a motor choke.
From 164 feet to 660 feet (200 meters) you can use the LR filter cell or a motor choke.
No there is no escutcheon for the INS40 - 160 range
The only difference between the 8020SCP423 and 8020SCP424 SY/MAX controllers is the size of their user memory. The 8020SCP423 has 8K of RAM. The 8020SCP424 has 16K of RAM.
As per the catalogue lsth050wh is supplied with a 16W driver. The LED strip kit has 4.8W/m. So theoretically when the strips are connected in series, 3.3 metres can be run off a driver.
We can make it up with following two items:
Part number LV431403 - NSX250F Basic Frame
Part number LV430470 - Micrologic 2.2 Trip Unit 160 Amps
How to configure Windows to use PowerChute Business Edition SNMP in conjunction with Windows SNMP and SNMP Trap Services.
PowerChute Business Edition versions 10.0 and above
NOTE: PowerChute Business Edition versions 9.2.1 and below use the Windows SNMP service, see FA159596 for more details.
All supported Windows operating systems
Windows SNMP Setup
Alternatively, you can directly access the Windows features dialog box by clicking on the Start button and typing “Turn Windows Features On or Off”.
- Open “Programs and Features” by clicking the Start button, selecting “Windows System” > “Control Panel” and then clicking “Programs and Features”. From within “Programs and Features”, select “Turn Windows Features On or Off”:
- Scroll down and enable “Simple Network Management Protocol (SNMP)”:
PowerChute Business Edition Setup
- Install PowerChute Business Edition if necessary.
- Enable SNMP v1 and/or v3 from the SNMP Settings screen if necessary.
- In the “Miscellaneous” section, update the Discovery Port from 161 to a free port e.g. 163 (161 and 162 are the well-known SNMP ports). If you do not make this change, you will see the error below. Click Apply to save your changes.
Remove conflicting Registry entry
- Click on the Start button, type regedit to launch the system registry editor and delete the following registry Key:
"1"="SOFTWARE\APC\PowerChute Business Edition\agent\snmp"
- Open Control Panel - Administrative Tools - Services and restart the PowerChute Windows Service
APC PBE Agent Service
- Restart the Windows Services
- Create a new PowerChute Agent IP/Port (Port from Step 5) mapping entry in your NMS.
- Test your changes.
You should be able to send traps from PCBE Agent to NMS (on SNMP port 162).
You should be able to query agent from NMS on new mapped port (e.g. 163, or your configured port in in step 5).
If PowerChute Agent SNMP Traps are configured, you can test real SNMP Traps test by doing a Lost Comms Test.
The digital outputs from the expansion card are true high, 24 volts sourcing. However, the digital outputs located at the drive X3 connector are true low, 24 volts sinking. A sample schematic is shown in the attached document.
Legacy KB System (APS) Data: RESL157164 V2.0, Originally authored by DaRo on 03/01/2012, Last Edited by MiOB on 03/01/2012
Related ranges: Lexium 17D
The below list are all measured in mm - all Reed Switches are Normally Closed with the magnet in place (NC)
5460 18h x 19w x 13d
5460HD 88h x 38w x 10d (cable lenght: 280)
5460RF 78h x 73w x 27d
When attempting to connect to a serial device in ION Setup a user receives the message: ‘Serial port not available’.
ION Setup Serial Connections
By default ION Setup supports 16 serial connections and 240 TCP connections. (TCP connections are defined as sites where one can have, say 10 Ethernet devices, connected to a single Ethernet site which will not be counted as 10 TCP connections).
This default division between serial and TCP connections can be controlled by modifying a setting located in the IONSETUP.INI file. Please change the ‘SerialPorts’ to the desired number from 16. Save the change before exiting the file.
You can locate the directory that contains the IONSETUP.ini file by opening ION Setup and selecting "Tools -> Options -> Directories"
The "Config Directory" file path is where the IONSETUP.ini file is located.
Change the value from 16 to 17 to gain an additional serial port.
Please note, the serial port number increment will take place in expense of TCP ports. So, if we increase the serial connections to 17, there will be 239 TCP connections available.
The PDL600RM is rated 16A resistive (6A inductive) and has a NO & NC contact. It is a 600 series module so can be mounted in a grid plate, but doesn't have to be as there is no built in indication as to the state of the contacts.
No - for 160 , will need to use NSX160, depth = 126mm
MCB maximum size 125A
The difference between the 8020SCP424 and 8020SCP444 SY/MAX controllers is the memory type utilized. Both units have 16K of user RAM; however the 8020SCP444 also offered 11K of nonvolatile memory for program storage on UVPROM.
Maximum drop length is 164 feet.
Minimum drop length is 8.5 feet.
Maximum trunk length is 8400 feet using RG11 and 4600 feet using RG6.
Maximum overall attenuation for the network is 35 db.
Minimum distance between taps is 8.5 feet.
Minimum distance between the RIO head and the self terminating "F" adapter is 18 inches.
Minimum distance between the self terminating "F" adapter and splitter 8.5 feet.
The following chart lists all current Quantum CPUs and their processor clock speeds:
Processor / clock speed
186 / 20 MHz
186 / 20 MHz
486 / 66 MHz
586 / 133 MHz
486 / 66 MHz
586 / 166 MHz
586 / 266 MHz
586 / 266 MHz
NetBotz 750 camera thumbnail must be manually deleted from surveillance view in StruxureWare Data Center Expert
StruxureWare Data Center Expert (DCE)
Camera Pod NBPD0165
NetBotz 750 / 755 version 5.2 firmware with a camera pod 165 in Surveillance View of DCE 7.7
Cameras are added to DCE in a different manner on a NetBotz NBRK0750 or NBWL0755
When you remove a version 2 or 3 NetBotz appliance with a camera pod 120 or 160 from a DCE server, the camera thumbnail will automatically be removed with the device. This is not the case with the NetBotz camera pod 165. Even after you remove the appliance from the monitoring perspective of DCE, the camera thumbnail will remain. To remove this thumbnail, you must right click the image and choose the "Delete" option.
Not available in NZ rewire with 56 series
Plate size: 66mm diameter
Mounting Centres: 50mm
Rated at 230V - 240V a.c. 16A resistive, 16A inductive 8AX fluorescent
The RCD itself has a max rating of 16A. However this product only comes with 10A rated plug and socket attached.
Yes - the standard saturn mechs (60PB) are rated at 16AX/20A
CCT15838 - Prog. time switch 16A IHPplus 1C 18 mm. This only has 1 N/O contact.
The alternative Acti 9 conversion is the A9F45316 3 Pole 16A 6kA MCB
No. - The 56 Series plugs only come with 16A or 20A 7 pin plug, as do the sockets.
Yes, the part number for a 3 position marked "1, 0, 2" 2 pole cam switch 16A is a 7GN12/52/U.
Rotary Cam Switches and Accessories, Rated Thermal Current (Ith) = 12A AC23A rating - 6kW at 415V. Rated Insulation Voltage Ui = 480V. Maximum 16A Fuse (gG/gL) for 3kA short circuit protection, 2 Pole 12A 60° changeover switch with Off marked 1-O-2.
Some of the key features are:
- Front mounting
- AC23A Rating
- Changeover switch with OFF marked 1-O-2
For further information please visit https://www.clipsal.com/Trade/Products/ProductDetail?catno=7GN12/52/U
The Acti9 A9F44216 is a 2p 16A C curve 6kA MCB.