Frequently Asked Questions
This is part of the old Clipsal 6 series contactors which are no longer available .It is an old Clipsal overload, which would need to be changed over to a Schneider LC1D range contactor with overload to suit . Over load to use is either LRD21 for 12-18A or LRD16 for 9-13A
For correct selection of contactor and overload required please call Schneider Electric on 1300 369 233
LA7D305 and LAD7305 Difference
IEC contactors and starters
Choosing the correct part number
LAD7305 is for use on LRD01 to LRD35 , LR3D01 to LR3D35, and LRD313 to LRD365.
LA7D305 is for use on all other relays (except LRD01 to LRD35 and LR3D01 to LR3D35).
This LRD range cannot be put back to Manual reset, once the overlaod has been changed from Manual (factory default) to Automatic.
LA7D3064 with LC1D compatibility
Tesys and Pre Tesys D-line
Fit, compatibility, and product features
The LRD3*** LR3D3***, LR2D35** D-line overload relays.