Frequently Asked Questions
Can we use the LAD4BB with the LC1D12BD?
IEC contactors and starters
Tesys D contactors
Identifying product compatibility
The LAD4BB will not work on the DC contactors, just the AC contactors.
Tesys D line Contactors and Accessories
Mounting this module to TeSys LC1D40A through LC1D65A contactor requires the use of the LAD4BB3 wiring adaptor. This adaptor can be fitted only to contactors with no coil suppressor.
On a TeSys D or TeSys IEC relay, is there a top mounting provision that will allow you to relocate the A1 & A2 terminals from the right side to the top?
TeSys D LC1D09-LC1D65A, TeSys IEC relay CAD**
The current TeSys IEC D line contactors ( LC1D09-LC1D65A) and the TeSys IEC Relay (CAD**) have A1 and A2 Terminals located on the right side of the device. To relocate the A1 & A2 Terminals, consider using the LAD4BB top-mounting wiring accessory. Please note this device can only be used on the D line contactors or the IEC relays that are provided with AC coils. A mounting accessory for units with a DC coil is not available.