Frequently Asked Questions
Can the old D-line attachments fit the new CAD relays
Tesys D contactors and relays
Using old accessories with new CAD relays
Yes, the old style front mount latch attachments, timing attachments, and auxiliary contacts will mount on the new Tesys D-line relays.
The replacement part number will be LADN31.
Checking on the DC current contact ratings for the CAD50, CAD32, CAD503, CAD323, CAD506, and CAD326 relay.
CAD Industrial Relays
Relays and Timers
125V DC - 0.55 Amps make and break, 2.5 Amps cont.
250V DC - 0.27 Amps make and break, 2.5 amps cont.
600V DC - 0.10 Amps make and break, 2.5 Amps cont.
What is the LA1KN** auxiliary contact rating?
LC1K, CA2K and CA3K, K-Line Tesys K
The auxiliary contacts are rating for 10 amps continuous.
The Auxiliary is an LADN31