Frequently Asked Questions
Powerpact L, I-line version
The I-line version of the Powerpact L Circuit Breaker requires 6 inches of bus. This is sometimes referred to as the "mounting height requirement".
What is the difference between the LUA contact blocks and the LUF contact blocks on a TeSysU motor starter?
TeSysU Simple Motor Starters
The LUA contact blocks are for signalling and will change state depending on mode or fault condition(s). These consist of one "Ready Condition" contact that operates with the handle and one "Fault Condition" contact that operates only when a fault is seen. The LUF contact blocks are standard contact blocks and will change state with the poles.
Yes, the exact replacement for VRDM397/50 LNA OOIP41 with ID number 52025015000 can be ordered using the new Schneider Electric ordering number of BRS397NS0010
The Schneider Electric reference number of BRS368H130AAA is now used to order the exact replacement motor for Berger Lahr type VRDM368/50 LHA with ID number 52024045000.
The replacement will be the exact replacement, only the part number has been changed to a Schneider Electric part number.
It is the position of the RI operating mechanism on SF1 circuit breakers fixed version.
You will find the explanations in the document (ppt) attached
Checking on the current rating of a 9080LBA363206.
9080LB Power Distribution Block
It is 350 amps for copper wire and 270 amps for aluminum wire.