Frequently Asked Questions
In which contactors can the LA1DN and LADN auxiliary contacts be mounted?
Auxiliary contacts for the Tesys D line
Tesys D-Line and Tesys F
These contacts will only fit on the following contactors:
Front mount only for LC1D40 through LC1D115 devices and LC1D40A - LC1D65A.
Left side mount only to LC1F contactors
Follow the attached document instructions:
The LX9FF110 coils have a rating of rating of 110...115 V AC 40...400 Hz
The older coils LX1FF110 that may be in older catalogues had a fixed frequency of 50 Hertz.
The LRD43xx type of thermal overload relays are directly mounted to the contactors LC1D115 & LC1D150 only. There is no separate mounting kit for the LRD43xx.
If a separate mounting is required for the contactors LC1D115 or LC1D150 type, then LRD336xx shall be selected as these range of overload relays have indepentdent mounting and have similar setting range and are of Class 10A.