- Can the Primary and Secondary be run together?
Preferably not - but this is impacted by the distance they are run together. If the distance is short, i.e. a few metres then not a problem. If it is more distance then need to segregate. It is difficult to give an exact answer as there are dependencies. If they were separate by 1m then any distance would be ok.
- Is segregation required, and if so what is the advised segregation distance and type (conduit etc)
As above - at least 1m would meet all circumstances. Type of conduit does not really matter as the distance provides the segregation rather than any shielding from conduit.
Please see following link for further information and related products