Frequently Asked Questions
The replacement part code is CAD50U7
Checking on the DC current contact ratings for the CAD50, CAD32, CAD503, CAD323, CAD506, and CAD326 relay.
CAD Industrial Relays
Relays and Timers
125V DC - 0.55 Amps make and break, 2.5 Amps cont.
250V DC - 0.27 Amps make and break, 2.5 amps cont.
600V DC - 0.10 Amps make and break, 2.5 Amps cont.
Identifying power terminal lug data for the D2 style contactors
IEC Contactors and Starters
Tesys D line contactors
Power terminal lug data required
For contactors with screw clamp terminals:
stranded cable w/o cable end : One #10-3 AWG or Two #10-4 AWG per terminal.
stranded cable w/cable end: One #10-4 AWG or Two #12-2 AWG per terminal.
solid cable: One #10-3 AWG or Two #10-6 AWG per terminal.
What is the altitude derating for a TeSys D-Line contactor?
Digest 177 Section 18 : Contactors and Starters, IEC
North American Products
The contactors are fully rated up to 3000 meters. Following are derating multipliers for altitudes above 3000 meters for both voltage and current:
3500m x 0.90
4000m x 0.80
4500m x 0.70
5000m x 0.60
3500m x 0.92
4000m x 0.90
4500m x 0.88
5000m x 0.86
For example, an LC1D80 at 5000 meters:
- The maximum rated operational voltage is 1,000V (IEC947-4) and 690V (UL/CSA). At 5000 meters it becomes 1000V x 0.6 = 600V (IEC947-4) and 690V x 0.6 = 414V (UL/CSA).
- The maximum rated operational AC3 current is 80A. At 5000 meters it becomes 80A x 0.86 = 68A.
What is the hot and neutral on the coil terminals for CAD50BL?
Tesys D IEC Style Relays
Determine if relay will work for a specific application.
Yes, the DC coil is polarity sensitive - A1 is positive and A2 is negative.