Frequently Asked Questions
Checking on the DC current contact ratings for the CAD50, CAD32, CAD503, CAD323, CAD506, and CAD326 relay.
CAD Industrial Relays
Relays and Timers
125V DC - 0.55 Amps make and break, 2.5 Amps cont.
250V DC - 0.27 Amps make and break, 2.5 amps cont.
600V DC - 0.10 Amps make and break, 2.5 Amps cont.
The replacement part code is CAD50U7
Identifying power terminal lug data for the D2 style contactors
IEC Contactors and Starters
Tesys D line contactors
Power terminal lug data required
For contactors with screw clamp terminals:
stranded cable w/o cable end : One #10-3 AWG or Two #10-4 AWG per terminal.
stranded cable w/cable end: One #10-4 AWG or Two #12-2 AWG per terminal.
solid cable: One #10-3 AWG or Two #10-6 AWG per terminal.