Frequently Asked Questions
That is a 3 phase, 12 pole supply with 27mm spcaing. It will supply up to 4x 3 pole breakers.
What is the temperature that will make the Micrologic A, P, and H trip with Ap fault indication?
Micrologic (proxima) trip units on Powerpact P, R and Masterpact NT, NW
Around 115 C, 239 F
CTA-ID : 2023723
ZB2Bxx sub-bases are made of chromium plated ZnAl4.
For the customized distribution board for 72 pole (18 mm) and 12 pole (27 mm) chassis, you need to submit request for a quote to "email@example.com". Our Standard distribution board only goes up to 60 pole (18 mm) and 12 pole (27 mm).
What is the heat dissipation (Watts loss) for the ATS22 series soft starters?
ATS22 soft starters
All models listed in the attached chart, all serial numbers
Customer unable to find needed information
Please see the attached file for the heat dissipation data for the ATS22 series soft starters.
Need the cutout diagram for the SEPAM 80.
SEPAM Series 80
Attached is the cutout diagram for the all SEPAM Series 80.