Frequently Asked Questions
For the customized distribution board for 72 pole (18 mm) and 12 pole (27 mm) chassis, you need to submit request for a quote to "email@example.com". Our Standard distribution board only goes up to 60 pole (18 mm) and 12 pole (27 mm).
NetBotz Rack Access AP9361 does not discover when choosing NetBotz discovery in StruxureWare Data Center Expert (DCE).
StruxureWare Central / DCE
NetBotz Rack Access AP9361 discovery in StruxureWare DCE
The NetBotz Rack Access AP93610 is based on technology from the earlier APC network management cards. This was similar to the Network Management cards in other APC devices. NetBotz 300, 400, and 500 series units are discovered using HTTP or HTTPS based on individual configuration.
Because the code in the NetBotz Rack Access AP9361 is not the same as the 300, 400, and 500 series NetBotz appliances, it must be discovered as an SNMP device in StruxureWare DCE. It can not be discovered using HTTP or HTTPS in DCE.
Using an ATV12 drive on 230vac 1 phase input and getting 230vac 3 phase output.
Needs to feed the drive 1 phase input and have 3 phase voltage coming out of the drive.
You can use the ATV12 version with the suffix M2 for 230vac 1 phase input and it will give you 230vac 3 phase output.
Please keep in mind that the load coming off the output of the drive can only be a inverter duty rated motor. You can not use the drive as a phase conveter and power up a machine with contactors, transformers etc.