Configuration is different
699 - switch, socket, socket, switch
699TB - switch, socket, switch, socket
Plate 48mm (H) x 170mm (W)
Mounting Centres: 150mm
Suits PDL 567L mounting Block & PDL 559 Mounting Bracket
There is no metal cover available for the 699 There is only a metal cover for the 699TB version
PDL 699 has one set of terminals and the PDL 699TB is the twin base model and therefore has a set of terminals for each outlet. The configuration of the switches and sockets
are different as well.
No - Rated at 15A = PDL694/15WH
RM 79 696 043: operating temperature.
The maximum operating temperature is 60°c.
Legacy KB System (APS) Data: RESL197838 V1.0, Originally authored by LaBe on 02/18/2009, Last Edited by LaBe on 02/18/2009
Related ranges: Zelio Control
Yes the 6CLK80 is a straight mechanical interlock to suit the 6C9 - 6C38 contractors.
Yes, the PDL 699CWH is the white cover plate to suit the PDL 699.
As a general rule of thumb -
PDL items require PDL at the front of the code.
600 series item codes start with 6.
600 series switch codes start with 68.
The number of switches fitted in the plate is the 3rd number in the code, 681 = single 600 series switch, 682 = double 600 series switch
600 series socket codes start with 69.
The 3rd digit in a socket code indicates the type of socket, 691 = single vertical socket, 692 = double vertical socket, 694 = single horizontal socket, 695 = double horizontal socket.
Most codes require a colour code at the end, WH = white, BK = black.
eg. To order a black double vertical switched socket the complete code would be PDL692BK.
800 series (Modena) item codes start with 8 and follow the same format as above. (800 series items with Strato plates start with S8...)
eg. An 800 series Modena double switch in white = PDL882WH, a Strato double horizontal switched socket in black = PDLS895BK
In both series metal cover plates are an extra option to be supplied separately, coded to fit the plate required, eg. 600 series single switch metal plate in Stainless Steel = PDL681MSS (M = Metal, BBZ = Brushed Bronze, PB = Polished Brass) Some plastic cover plates are available eg. PDL681CWH (C = Cover), PDL800PSCH (PS = Plastic Surround, CH = Champagne, there are 9 colour options in 800 series)
Strato brushed aluminium plates also need BK or WH to decide the trim colour, eg. PDLS800CBABK or PDLS800CBAWH (C = Cover , BA = Brushed Aluminium)
Module grids with covers are available in BK or WH, eg. PDL684VHWH (VH = vertical/horizontal since the grid is empty and module can be fitted either way), PDLS800GPSBK (GPS = Grid, Plate, & Surround).
Grids without covers included are only available in Modena 800 series, PDL800G (horizontal) or PDL800GV (vertical)
Refer pdl.co.nz for further details and options.
You can purchase PDL 695X and the pdl indicator module that is required
The part number is PDL695CWH
This error will occur when selecting a PLC type other than a Compact , Momentum or Micro PLC with an authorized Lite version of the ProWORX NxT software.
The Lite software will operate like a Full version when in DEMO mode, but once authorized as Lite version it will be limited to these three PLC types.
Not available in red as a cover only, can purchase the complete unit in red (PDL 691RD)
No, They are not available in Ivory colour.
Time Ranges available on the 9050JCK70
Class 9050 Type JCK Timers
North American Products
The 9050JCK70 has 5 selectable timing ranges:
0.5 to 9.99 seconds
0.1 to 99.99 seconds
1 to 999 secconds
0.1 to 99.9 minutes
1 to 999 minutes.
User wants to use three phase 120V L-N through a potential transformer for control power to the CM4000 that is 69V L-N
|Yes, the circuit monitor can be used with line-to-line rated PT's connected line to neutral, which results in a line-to-neutral voltage of 69.
How do you wire a CA2DN40?
A1 and A2 are the coil connections, line connections at top, load conections at bottom, example for 1 contact,in at top is #13, out at bottom is #14.
The cover (PDL 691C) for the PDL 691 is only available in White (691CWH), Polished Brass (691MPB), Brushed Bronze (691MBBZ) and Stainless Steel (691MSS). Black is not available.
From what key number from the 9001KS/SKS keyed switches uses the E99 master key?
No, only E36 thru E60 will accept the master key.
ATV28 Menu is locked from the front panel? Already tried to enter 6969 and 0 for password unlock, but won't work. The keypad is always locked. Only access to the drive is through PowerSuite or Remote Keypad Vw3a28101.
Please retry it with a pressure of 2 sec on the Enter key but there is also a bug with the versions before v1.1 ie12.
Legacy KB System (APS) Data: RESL159990 V1.0, Originally authored by on , Last Edited by on
Related ranges: Altivar 28
A CM2000 can be assigned an address from 1-199; however, should address 199 be used?
Address "199" should always be reserved. The circuit monitor will accept 199, but this is the address that the Circuit Monitor defaults to in a failure situation.
For steps on setting the CM2000's device address, please refer to FA218954.
Use a PDL695X and put a PDL600SM in the extra mech space
PDL has a small surge mdoule which can be installed into any 600 series switch hole.
600 series Surge Module Surge Protection
NOTE: new commercial reference found might not be an exact 1:1 equivalent of the older commercial reference. Contact us on 0800 652 999 with the application details if you need to confirm.
The cover to suit the PDL 695 is a 695C.
We only do a horizontal single, switched socket with two extra switches - PDL 694XX.
Another alternative would be to use a PDL 691X. This is a vertical single, switched socket with one extra switch.
How to read energy values off the front panel display of ION 6200 meter.
ION 6200 front display reading energy values
Energy values are often directly read off the front panel display. However, the 6200 Installation and Operation Guide do not explicitly describe how to get these energy values.
The KWh front panel display constitutes of three rows. Say that the first row of the KWh display is showing 'aaa', the second row shows 'bbb' and the third row shows 'ccc', then the total KWh read by the meter is aaa bbb ccc KWh.
The 6200 is hard-coded to roll over at 100 000 000 KWh. As the KWh starts accumulating, the third row on the display shows an increment in value. When the value goes over 999 KWh, the second row is used to display the KWh values up to 999 999 KWh. Eventually, when the value goes over 999 999 KWh, the top row is also used to display the KWh until the KWh rolls over at 100 000 000 KWh.
Example: As shown in picture below (from ION 6200 front display), the total kwh accumulated is = 270,050 kwh
As of right now, no ION hardware undergoes any testing for seismic and/or vibrational compliance. No meters in the ION family have this compliance. Typical standards are IEEE 693 and IEC 60255-21-3.
Date Created: November 12, 2010
Last Revised: November 18, 2010
Original Author: DD
All content © 1992-2010 Schneider Electric
Legacy KB System (APS) Data: RESL203933 V1.0, Originally authored by LaAd on 11/19/2010, Last Edited by LaAd on 11/19/2010
Related ranges: ION8600, ION75X0 RTU, ION7550/ION7650, ION7300, ION6200
Master password to reset the ATV11 drives.
Password has them locked out of the drive.
Menu SUP then COD enter master password 696 to unlock the drive.
The 3710 Modbus protocol supports both 16-bit and extended 32-bit registers (the register size is selectable from the front panel). 32-bit registers are used for large value such as energy values while 16-bit registers are used for other parameters, such as current or voltage.
The kWh is rolling over at 65535 since it is being read as a 16-bit register, but it should be a 32-bit value; only the low byte of the 32-bit register is being read. Changing the modbus read mode to 32-bit will provide the correct kWh reading.
Last Revised: 4 July 2007
All content © 1992-2007 Schneider Electric
Legacy KB System (APS) Data: RESL186856 V1.0, Originally authored by KBAdPM on 07/11/2007, Last Edited by KBAdPM on 07/11/2007
Related ranges: 3710 ACM
What is the ATV320 universal pass code to unlock the drive?
Product Line :
ATV320 STO password reset.
Universal passcode is 1581
"When attempting to connect a system running PowerChute plus in simple signaling through an Isolated Extension Cable (IEC), you must use a 24VDC adapter to power the UPS End Unit of the IEC.
The server side is powered off of the serial port itself. Therefore, the DC adapter is not required. This adapter is available for purchase on APC's Web site (www.apcc.com). Users may also find an equivalent power adapter at their nearest electronics store. The specifications for the 24VDC adapter follow:
Input: 120 VAC 60Hz 16W
Output: 24VDC 400mA"
Below is a table of how Severity(APM) corresponds to SMS alarm and Meter onboard alarm level.
APM SMS Onboard Alarm Level
1000 Comms Loss
900 1 1
800 2 2
700 3 3
Please note it's always best practice to have the severity +/-1 of the severity level.
For Example: If the customer wants only Level 4 Alarms, a filter would be created with severity from 599 to 601.
Legacy KB System (APS) Data: RESL206964 V1.0, Originally authored by MaTh on 12/22/2011, Last Edited by MaTh on 12/22/2011
Related ranges: SMS Add-on, Paging Module
What is the tripping current for a Multi 9 GFP Ground Fault Protector?
Multi 9 C60 Ground Fault Protectors
Tripping currents are as follows:
GFP30 Must trip at 29.9 mA; must not trip below 22.1 mA
GFP100 Must trip at 98.9 mA; must not trip below 73.1 mA
GFP300 Must trip at 299 mA; must not trip below 221 mA
What is the heat loss for the ATS22C32S6U?
Heat loss :
During starting @ 3.5 ICL (Nominal current of the softstart) : 3699 Watts
During Steady State at full load : 96 Watts
Electronics : 20 Watts
Shorting Contactors : 14 Watts
Fans : 20 Watts
Total at Steady State : 150 Watts
Video: How to lock or unlock an ATV320 drive?
User may need to temporarily lock the drive's programming from unwanted changes.
Enter and scroll down into COD-
COD is for PIN code 1
COD2 is for PIN code 2.
If the pass code needs to be unlocked, assigns pin code 6969 for Pin code 1 to unlock it.
Once the unit is unlocked, you can change the PIN code 1 to OFF in order to turn off pass code protection.
CST is state of password:
LC (Locked): The drive is locked by a password
uLC(Unlocked): The drive is not locked by a password
The alarm log is a circular buffer. It means that, once it filled up, new alarm events will overwrite the oldest alarm events. For example, if your alarm log size is set to 100 records, it will work like this:
- events 1 to 100 will fill up the alarm log.
- event 101 will overwrite event 1.
- event 102 will overwrite event 2.
- event 199 will overwrite event 99.
- event 200 will overwrite event 100.
- event 201 will overwrite event 101.
Legacy KB System (APS) Data: RESL183431 V1.0, Originally authored by MiMe on 04/10/2007, Last Edited by MiMe on 04/10/2007
Related ranges: Vijeo Designer
What is the master unlock code for an ATV320 PIN Code 1?
Altivar 320 drives
User needs to unlock a drive that was locked with PIN code 1, and the code was forgotten/lost
PIN code 1 has a master public unlock code 6969
For more information on PIN code 1, refer to the ATV320 Programming Manual pages 75 and 300
Symmetra LX runs on battery and may exhibit audible clicking from the power modules. Erroneous messages regarding output voltage may also occur. If the SYMIM5 firmware is rev 512 or above, the UPS may show "Site Wiring Fault."
All serial ranges
A neutral wire is needed in order for the Symmetra LX to operate online correctly. A missing neutral or a neutral that is not properly bonded to ground at the upstream panel or transformer can cause the UPS to exhibit the symptoms above.
If these symptoms are present, an input wiring check should be completed to ensure a neutral is being fed to the UPS and is connected to the correct terminal. The neutral must be properly bonded to ground. Without one, the Symmetra LX will not operate properly.
To upgrade the copro firmware of the 140CPU67160 (using OSLoader), you need to use the fibre optic MTRJ port and switch which as fibre optic and electrical RJ45 ports (such as the 490 NOC 000 05 cable and 499 NOS 171 00 switch).
There are no other method available at this moment.
Other related information
To upgrade the firmware of UNITY Quantum CPUs (using OSLoader), you can either use one of the following way:
- Modbus (with address 1 only)
- Modbus plus (with address 1 only)
To upgrade the copro firmware of HE 140CPU65150 and 140CPU65160 (using OSLoader, you need to use the ethernet coneection via FTP.
Legacy KB System (APS) Data: RESL168369 V1.0, Originally authored by on , Last Edited by on
Related ranges: Modicon Quantum
The Short Circuit Current Rating (SCCR) for Altistart 48 Range of Soft Starters is as follows:
For Q series:
1. SCCR for ATS 48D17x to ATS 48C32x is 50 KA.
2. SCCR for ATS 48C41x to ATS 48M12x is 70 KA.
For Y series:
1. Refer attachment for the Short Circuit Protection Device (Type 1 Coordination).
What is the input voltage tolerance on the ATV61 and ATV71 VFD?
Altivar 61 & 71
All models, All serial numbers.
Input voltage tolerance range needed.
For single phase input, part # ATV61H075M3 through ATV61HU75M3: 200 -15% to 240 +10%
For three phase input, part # ATV61H***M3 and ATV61H***M3X: 200 -15% to 240 +10%
For three phase input, part # ATV61****N4 and ATV61W***N4C: 380 -15% to 480 +10%
For three phase input, part # ATV61H***Y: 500 -15% to 690 +10%
For single phase input, part # ATV71H075M3 through ATV71HU75M3: 200 -15% to 240 +10%
For three phase input, part # ATV71H***M3 and ATV71H***M3X: 200 -15% to 240 +10%
For three phase input, part # ATV71****N4 and ATV71W***N4C: 380 -15% to 480 +10%
For three phase input, part # ATV71H***Y: 500 -15% to 690 +10%
Can your InRow Cooling Auto-Start after a Power Failure
Data Center Cooling
The InRow RC, RD, RP and SC will start automatically if the power is restored after a power failure. The unit will go to its last known state, ie if the unit was in standby, the unit would return to standby, or if the unit is on, the unit would return to the on state.
It is also possible to configure a Start up Delay of 0 to 999 seconds.
That can be done from:
- The Display: Configure Unit>General> Startup Delay
- The Network Management Card Interface: Unit>Unit Configuration> Startup Delay
Comment fonctionne les compteurs d'énergie de l'ATS48.
Il existe 2 compteurs:
- le compteur en kW ( puissance active ) de 0 à 999 kW;
- le compteur en kW/h qui nécessite le fonctionnement du démarreur pendant au moins une heure ( pour la première ). Son échelle est de 0 à 65535, soit 7,4 années ( 7j/7 et 24h/24 ).
Meaning of Trip Classes for overload relays.
NEMA Overload Relays
North American Products
The trip class means that at 600% (6 times) of the maximum thermal current rating (or 600% of the actual dial setting on adjustable overloads) the Class 10 will trip in 10 seconds or less, Class 20 will trip in 20 seconds or less, and Class 30 will trip in 30 seconds or less.
What minimum voltage is it possible to use ATV68, when switching-off protection undervoltage? Thank you very much for your help.
400 V range = 287 V
500 V range = 346 V
690 V range = 537 V
If the control is supplied with an external source 24V, if the voltage goes under the guarantied range, and if the fault undervoltage is deactivated (E3.08), the drive is going to supply the motor in downgraded operation (speed reduction, current limitation...) as long as no other fault appears.
Legacy KB System (APS) Data: RESL161862 V1.0, Originally authored by on , Last Edited by on
Related ranges: Altivar 68
Request for the short circuit ratings of the SYBTU1, and SYBTU2 batteries.
Symmetra PX, Smart UPS VT
All models, all serial numbers
Request for information on the short circuit ratings of the battery modules used in the Symmetra PX and Smart UPS VT systems.
The short circuit rating of the battery module is limited by the fuses inside it. The SYBTU1-PLP, and SYBTU2-PLP battery modules have fuse part #515-1063-Z.
Fuse Fast 63 Amp 500 VDC / 690 VAC ROHS
Bussmann Spec Sheet attached.