Powerpact H, J, L, M, P and R
There are two terminals on the UVR and the Shunt Trip accessories to which you attach the control wires.
- The shunt trip will trip the circuit breaker if control voltage is applied across the two shunt trip terminals.
- The undervoltage trip will trip the circuit breaker if control voltage is removed from the two undervoltage trip terminals.
Here are links to the instruction bulletins for the shunt trips and undervoltage trips of the Powerpact Breakers
Powerpact H, J, L - document 48940-229-01
Powerpact M, P, R - document 48049-245-03