Frequently Asked Questions
No - PDL692CWH only
or the metal plate options:
PDL692MSS - Stainless Steel
PDL692MBBZ - Brushed Bronze
PDL692MPB - Polished Brass
The PDL 692XC is the cover plate to suit.
Yes as of December 2015 the 642MUSB mech can be installed into the extra mech position of the 692X or 695X
This is also available as complete units:
No, They are not available in Ivory colour.
Symmetra LX runs on battery and may exhibit audible clicking from the power modules. Erroneous messages regarding output voltage may also occur. If the SYMIM5 firmware is rev 512 or above, the UPS may show "Site Wiring Fault."
All serial ranges
A neutral wire is needed in order for the Symmetra LX to operate online correctly. A missing neutral or a neutral that is not properly bonded to ground at the upstream panel or transformer can cause the UPS to exhibit the symptoms above.
If these symptoms are present, an input wiring check should be completed to ensure a neutral is being fed to the UPS and is connected to the correct terminal. The neutral must be properly bonded to ground. Without one, the Symmetra LX will not operate properly.