Questions about how much heat each part of a Conext system uses.
Conext Battery Based Inverters
Conext MPPT Solar Charge Controllers
Battery based inverter in an enclosed environment.
Proper system design needs to account for system cooling.
The power in BTUs per hour (BTU/hr) is equal to 3.412141633 times the power in watts (W):
= 3.412141633 × P(W)
The efficiency and load of each unit can be used to calculate power loss in watts and then the above formula can be used to convert to BTU/hr.
Conext XW+ 6848
Conext SW 4024 NA
92% efficient at 4000W = 320W losses = 1092 BTU/hr
Conext MPPT 60 150
98% efficient at 48V battery at 3500W = 70W losses = 239 BTU/hr
Conext MPPT 80 600
96% efficient at 48V battery at 4800W = 192W losses = 655 BTU/hr