Frequently Asked Questions
|There are 12 mappings, each mapping can have only 1 C-Bus group address, but as many DMX addresses as desired (one to many relation)
The replacement for a 5500CN is 5500CN2.
Continuously, press and hold down the page button (button 5) for 10 seconds.
The 5500CN2 is the replacement for a 5500CN
The 5500NAC or 5500SHAC can be used as Bacnet gateway depending on the number of Bacnet points which are required.
The 5500NAC has 500 Bacnet Points and the 5500SHAC has 50 Bacnet points.
Bacnet is normally used by Building Management systems.