Frequently Asked Questions
advised 891MA is socket module only and the 891A is fully assembled grid, plate, socket and switch
The dimensions are 121mm (W) X 83mm (H) X 155mm (D).
The LUCA12BL is to be controlled directly with the output of a PLC.
Tesys U line
PLC doing remote control of the motor starter.
Yes, if the output of the PLC is 24 V DC and can handle an inrush of 220mA . A reversing module will add 120mA to the inrush when it has to change the direction of the motor.
Software filter time parameter for TM2/TM3 analog input module is the time constant of the 1st order filter (or the time to reach 63% of the final value).
for example, for 4...20mA signal, it will take 20ms for the signal to change from 4mA to 12.6mA (20mA x 63%).
Cheching if Zelio relays can monitor negative currents.
Relays and Timers
Zelio Control and Measurement Relays
Documentation shows on 4-20mA does not clarify postive or negative.
Yes, the RM35JA31MW can monitor +4 to +20mA or -4 to -20mA.