No, unfortunately this mounting block is unavailable in black. As an alternative we can do the 448SD Mounting block in black however it has a depth of 14mm a pose to 28mm.
Some of the key features are:
- Large size format, deep mounting
- With metal inserts, 16 mounting screw positions
- Various colours available
For further information please visit www.clipsal.com/Trade/Products/ProductDetail?catno=448SD
The 448 should be used with a large plate Prestige switch.
This customer support bulletin identifies a potential issue with ION Enterprise 5.6 B447 and 448 when upgrading to Service Pack 2, and explains the resolution.
There is a problem with the ION E 5.6 SP2 Installer when executed against builds 447 and 448 of ION Enterprise 5.6. The problem results in an upgrade installation failure when run on a client machine, secondary server or database server. The upgrade of a primary server will succeed When the SP2 install fails, the customer is left with the pre-existing version (5.6 or 5.6 SP1). This rollback will not appear to impact the function of the client, secondary or database server, but will leave the customer with a system where the primary is using a different version than the other machines; an unsupported configuration which may result in data and connection errors. We have determined that the stated builds were delivered during May, June and July 2007. The issue does not affect build 449, which has been in release since July 31st, 2007.
A modified version of the service pack will be available for download from the website by October 13th, 2008, at 12:00 PM GMT. Any installation of Service Pack 2, whether by the customer or a proxy on behalf of the customer, must use the modified version. The modified version will work with build 449 as well.
The following workaround is available for customers unable to wait for the modified version of the service pack. However, as the workaround involves shipment and end-customer delivery of a CD, it is likely that downloadable service pack will be available by the time the workaround can be implemented. In addition, there are steps which should be taken in the event the customer needs to upgrade a database server, and we strongly suggest tech support be contacted if this is the case.
- Verify the customer is using build 447 or 448 of ION Enterpise 5.6, as the following is not necessary if they are using build 449. To verify, open the file "ION Enterprise5.6Setup.log" on the client, secondary or database server. Note: If you have previously installed Service Pack 1, open the file called "ION Enterprise_5.6_SetupLog(1).log" instead. The build will be listed on the 15th line, and will resemble "OK (0) ION Enterprise 5.6 build 448".
- Request a new ION Enterprise 5.6 CD via PMC Technical Support. All new versions use build 449.
- Upon delivery, uninstall ION Enterprise 5.6.
- Re-Install using the delivered CD.
- Install Service Pack 2. At this point, the version of the service pack is not of consequence, as there is no issue with build 449.
If you have questions about this bulletin, use any of the various means of contacting us presented on the following web page to communicate to us:
Last Revised: 22 Sept 2008
All content © 1992-2008 Schneider Electric
Legacy KB System (APS) Data: RESL192820 V2.0, Originally authored by DaMi on 09/24/2008, Last Edited by DaTh on 10/29/2008
Related ranges: ION Enterprise V5.6
Yes, we do have a deeper version of the 448SD, large format, mounting block. The part number is 448.
The depth of the 448SD is 14mm where as the 448 has a depth of 28mm.
No, the largest rated version of a 438 extension socket is the 438/20 which is 20A.
No it has been replaced by the spark-e-mate 493BTL and 493BTL I
No. This product is only available in white.
Levco are the suppliers of Hospitality cards +64 9 444 0161
The card is not supplied in the PDL626N pack.
Part no for mounting block is 447
The W48 warning comes on when I am inverting, and the Control Panel beeps and flashes.
XW, Conext XW+, Conext SW
Battery based inverters typically used off-grid, or during power outages.
W48 is related to F48. F48 is the Low Battery Cut Out Fault. In our inverter, the W48 warning appears when the battery voltage reaches the Low Battery Cut Out setting plus 2Vdc.
Acknowledge the fault, and recognize that the battery may need charging. The warning can be avoided by lowering the LBCO, but that also means that the inverter is allowed to use more of the battery when it is inverting. If a generator is available, this would be a good time to turn the generator on to charge. This can also occur if there is a large load that drags the battery bank voltage down while running. This type of scenario is fairly normal for smaller sized battery banks. The fault can also be cleared manually using an SCP or Combox if the battery voltage has increased past the warning threshold.
For discrete IO modules, you can have up to 488 digital IO counts.
For Analog IO modules, you can have up to 114 analog IO counts.
DC under-voltage shutdown (immediate) occurs if DC voltage is below 16 VDC (24 V system) or 32 VDC (48 V system).
XW Series Inverter Charger
Check for the correct battery voltage at the inverter's DC input terminals. Check for an external DC load on the batteries. Check condition of batteries and recharge if possible.
The fault clears and the inverter restarts when DC voltage reaches VLBCO+2 V (24 V system) and VLBCO+4 V (48 V system).
Are the Altivar ATV18 fault contacts dry?
Yes, you can supply up to 250 volts AC at .5 amp.
The input voltage selector must be adjusted in order to accommodate the new voltage requirement. This process is outlined on page 10 of the owner's manual
Yes. The XW Config Tool will work on a Windows 8 operating system provided you use the attached multi-driver and CnxtCfgTool software.
The Acti 9 Breakers can work up to 440 VAC as per typical data sheet
What is the right way to connect and chain the MET 148, MSA 141, and DSM 303 accessories on the Sepam 20 or 40?
On the D Port you have to connect and chain in order:
(1) MSA 141
(2) MET 148 ( Attention: Option 2 MET 148 for Sepam 40 only )
(3) DSM 303 (Always at the end of this chain and only if no more than 2 accessories already connected on Sepam)
Note: you can't connect more 3 accessories on this chain so if you already have 1 MSA 141 and 2 MET 148 it is impossible to set also 1 DSM 303. In this case if you want to put this DSM 303, you have to remove the MSA 141 or 1 MET 148.
Key words and phrases: MSA141, MET148, DSM303
Legacy KB System (APS) Data: RESL201098 V1.0, Originally authored by DaMi on 01/22/2010, Last Edited by DaMi on 01/22/2010
Related ranges: Sepam accessories, Sepam series 20, Sepam series 40
Ports used on InfraStruxure Central
StruxureWare Data Center Expert
InfraStruxure Central any version
StruxureWare Data Center Expert any version
The following outlines ports used and their application on any ISX Central Server:
Note: Ports or Protocols preceded by * can be changed from their default port number.
Port 80 (TCP/UDP) - *HTTP Communication from NetBotz Appliances / *ISX Central Console/Web API and 3rd party integrations.
*Port 443 (TCP) - HTTPS Communication from NetBotz Appliances / ISX Central Console
*Port 161(UDP), 162 (TCP/UDP)- SNMP Communication from SNMP Agent
*Port 502 (TCP/UDP)- Modbus TCP Communication from Modbus Device/Gateway Outgoing:
Port 80 (TCP/UDP)- *HTTP Communication to NetBotz Appliances / *ISX Central Console / HTTP Post to Web Server/Web API and
3rd party integrations.
*Port 443 (TCP) - HTTPS Communication to NetBotz Appliances / ISX Central Console
*Port 161 (UDP), 162(TCP/UDP) - SNMP Communication to SNMP Agent
*Port 25 (TCP)- SMTP Communication to Email Server
Port 21 (TCP)- FTP Communication to FTP Server
Port 123 (UDP)- NTP Communication to NTP Server
Port 139 (TCP/UDP)- SMB Communication to NAS / SAN
Port 53 (TCP/UDP)- DNS Communication to DNS Server
Port 111 (TCP)- NFS Mount
Port 2049 (UDP)- NFS Communication to NAS / SAN
Port 6000 (TCP)- APC Proprietary Communications protocol for use with AP76xx outlet strips and gen1 PDU on private lan.
Port 445 (TCP)- CIFS Communication to NAS / SAN
Port 502 (TCP/UDP)- Modbus TCP output to Building Management System
*Port 389(TCP/UDP)- Active Directory/LDAP
LV429210 - Is Vigi block MH type for NSX100/160 (200 to 440 V)
LV431535 - Is Vigi block MH type for NSX250 (200 to 440 V)
Even though Tech datasheet specifies the LV429210 is rated for NSX upto 250, It is recommeded to use the VIgi module only for NSX 100/160.
However, LV431535 can be used for NSX100/160/250.
For Sepam 80: what is the correct order for adding the accessories MSA 141, MET 148, DSM 303, and MCS 025?
The Sepam 80 has got 2 Ports. Using these, it is always possible to be able add all the different accessories that one might need for the Sepam 80.
On the D1 port, connect in order the MSA 141, next 1 or 2 MET 148 ( 1 MET 148 if you use also DSM 303) and next at the end the DSM 303
On the D2 port, connect in order the Second MET 148 and the MCS 025 at the end.
You can connect a maximum of three accessories on each port (D1 or D2).
The DSM 303 and the MCS 025 have to be always at the end of this chain. So if you use these 2 Accessories DSM and MCS on same Sepam 80, you have to use necessarily the 2 ports ( i.e. set the DSM at the end of D1 and set the MCS 025 at the end of D2)
Legacy KB System (APS) Data: RESL201116 V1.0, Originally authored by DaMi on 01/22/2010, Last Edited by DaMi on 01/22/2010
Related ranges: Sepam accessories, Sepam series 80
Yes, we do have a 5 pin 63A appliance inlet. The part number is WMB563R
Some of the key features are:
- 5 round pins
- 10 - 25 sq mm conductor terminal
- 1 gang
- Multi phase
- Overall dimension: 148 mm Height x 115 mm Width x 109 mm Depth
For further information please visit https://www.clipsal.com/Trade/Products/ProductDetail?catno=WMB563R
Contact Rating of 9013F Pressure Switches
Pressure, vacuum and Float Switches
9013 Type F Pressure Switch
Those contacts have a control circuit rating of A600.
They are DC rated at 1/4 HP at 115V and 230V (Except form M4)
They are Single Phase AC rated 1 1/2 HP at 115V, 2 HP at 230V
They are Polyphase rated 2 HP at 115V, 3 HP at 230V, and 1 HP at 460/575V.
This also applies to the 9013 FHG2, 9, 12, 13, 44, 49 9013 FSG, and FSW.
List of Device Definition Files (DDF) for Version 2 Netbotz Advanced Device Crawlers
NetBotz version 2
The following is the list of available device definition files (DDF) as of March 2009. Available DDF files:
The remote terminal VW3G48101 is delivered as a kit comprising:
- the keypad,
- a mounting kit containing a cover, screws and an IP 54 seal on the front panel to be positioned on the door of a floor-standing enclosure,
- a 3 m connecting cable (SUB_D9/RJ45).
The keypad itself is not UV protected, but the mounting kit uses a plastic material which is UV resistant.
Even though the mounting kit parts are UV resistant, note the following remarks:
- take care about the temperature (sunlight can warm up the keypad)
- direct sunlight on the screen display can reduce readability.
CTA-ID : 2062798
A Sliding Window is a variable receive buffer capacity that is advertised in the 16 bit Window packet section of the TCP Header. This is how a transmitting device advertises the current receive buffer capacity to the sender. The 174CEV30010 and 174CEV30020 Modbus to Ethernet bridges support a sliding window. For example, if the CEV buffer starts out at 512 bytes capacity and there is an outstanding Modbus message size of 14 bytes, the advertised window will be 498 bytes in the response. Note that most PLC services support a fixed receive buffer window size.
Legacy KB System (APS) Data: RESL173844 V1.0, Originally authored by on , Last Edited by on
Related ranges: Modicon Quantum
Testing XW AGS auto-start function
By setting the 30 second start voltage higher than the actual battery voltage, the auto-start function can be tested
as long as no grid voltage is passing thru AC1, otherwise the AGS will not be called upon to start.
Temporarily disable charge controllers to allow the battery voltage to rest. Make sure no sensitive electronics
are needed during this time because they may see the grid interruption and reset.
Make sure to set the 30 sec start voltage back down to a reasonable level after
test is completed. LBCO must be set lower than 30 sec start voltage.
Recommended settings :
30 second start V : 46.5 (23.5 for 24V model)
LBCO : 44V (22V for 24V model)
All other start/stop parameters should be disabled.
Do I need to use the stacking port when stacking two of the Conext SW?
System with two of the Conext SW inverter stacked in parallel
The stacking port is inactive and unnecessary for stacked Conext SW systems. Make sure the Xanbus ports are properly configured and there's a connection between the two units before starting them.
Purpose of stacking port isn't fully explained in the CSW manual
Multi 9 (M9) breaker and 480V breakers
Applies to Multi 9 (M9) circuit breakers
Need a 480V breaker in the miniature style.
No, the Multi 9 breakers are not rated 480V delta.
The UL 1077 listed M9 is rated for 480Y/277, not 480V delta.
The IEC version has a 440Vac rating
The UL 489 version has a 480Y/277vac rating (.5A-20A), 240 volts (.5 -35A).
For additional information on the ratings please see systems catalog in download center.
Reason for substitution: end of life
Substitution date: 30/12/2009
This product is replaced by:
LC1D40AN7 - TeSys D contactor - 3P(3 NO) - AC-3 - <= 440 V 40 A - 415 V AC 50/60 Hz coil
Details Returned from IBM Devices via Advanced Device Crawlers
NetBotz version 2 Advanced Device Crawlers.
The following information can be queried via Advanced Device Crawlers for IBM systems assuming the IBM DDF (Device Definition File) is installed on the NetBotz appliance and the IBM system is SNMP enabled. Please note that not all information listed below is available on all IBM models.
- Power Supply State
- System Thermal State
User wants to know what port the Com'X uses to upload data to cloud services Remote Service Platform (RSP)
Com'X uses port 443 with SSL to upload data to RSP.
Checklist for setting up an XW system for sell. See XW operation manual for full full details.
XW 4024 or XW 4548 or XW 6048 with f/w revisions 1.05 and above. MPPT60 or 80 charge controller. SCP
1) Enable Grid support in XW setup menu
2) Set Grid support voltage to 64V and enable SELL in XW advanced - grid support menu
3) Verify CHARGE CYCLE is '2stgnofloat' in XW advanced - charger settings - charge cycle (factory default setting)
4) On MPPT set CHARGE CYCLE to '3 stage' in MPPT advanced - charger settings - charge cycle
5) Is also recomended that the system has 100Ah for every KW of power that the customer wants to sell
ISX-GEN-ATS - 428 generic alarm
ISX-GEN-ATS – Cummins Diesel Generator
All models, all serial numbers
What does it mean when I get an “428 generic alarm” at my ISX-GEN-ATS Smart Gen ATS panel?
This alarm means “water in the fuel” go to Generator for more detail.
The alarm that’s set at the APC-Schneider ATS panel display is a generic Generator alarm/ event, to obtain more description you must go to the Generator and check the alarms. Use Fault Acknowledge button to clear the alarm at the generator. After the alarm has cleared at the generator then check the ATS alarm is also cleared, if it is not cleared then toggle the automatic operation switch from auto to manual (reset) and back to auto to clear any latched alarms at the ATS panel.
Cummins FSR/ Generator repair tech should be called to look over the Genset fuel system and determine how to fix and clear the alarms. It’s possible you have water in the fuel/ water separator filter and that would need to be drained. Otherwise, some sort of sensing failure of this water in fuel sensing circuit. Call your Generator service company
LC1K0910N7 replaces LC1K0910Q7 Contactor.
The coil is rated @ 415V AC but can operate at plus or minus 10% of coil votlage.ie Between 373.5V AC AND 456.5V AC
TeSys K contactor - 3P(3 NO) - AC-3 - <= 440 V 9 A - 400...415 V AC coil
For more information see;
The replacement for LC1D40004N5 Contactor is LC1DT60AN7
The substitution for sprecher schuh CA8-12C-1024D Contactor is LP1K1210BD
TeSys K contactor - 3P(3 NO) - AC-3 - <= 440 V 12 A - 24 V DC coil
No, unfortunately we do not have anything that matches those specifications exactly.
However we do have a product that is similar. The part number is OW5845
It is also a 240V cabinet fan.
Some of its key features are:
- Slim axial fan
- Body made from die-cast aluminium
- Impeller made from fibreglass reinforced with nylon
- 172 mm overall intake
- 148 mm diameter hole
- 38 mm Depth
- 1 speed
- Ball bearing motor
- -10 to 65 deg C maximum operating temperature
- With OW6421 protection grille
For further information and documentaion on this product please visit https://www.clipsal.com/Trade/Products/ProductDetail?catno=OW5845
XBTL1000 : Erreur "Application transférée Incorrecte" lors du transfert de l'application, suivi de
"Erreur interne de construction de la liste des fichiers à transferer " lors de la seconde tentative de transfert de l'application.
XBTL1000 V4.30 4.40 4.42 4.48 Application transférée Incorrecte transfert Erreur interne de construction de la liste des fichiers à transferer
Il se peut qu'un antivirus empêche la création ou l'écriture de fichiers .exe ou .dll.
Car lors du transfert d'une application XBTL1000 (même directement vers le terminal), une copie temporaire des fichiers est faite en local sur le PC.
Une désinstallation de l'antivirus (dans le cas particulier du client en question, Norton antivirus) permet de résoudre le problème.
A ce jour, un seul client a rencontré ce type de problème.
Criterion for relay contacts to be worn out electrically is contact resistance is >= 100 mOhm.
Given two contacts with 100 mOhm each in line and the thermal sum current of 10,5 A distributed over 3 channels in case of XPSAC gives a maximum heat dissipation of 7,35 W in the output channels of the XPSAC.
Given two contacts with 100 mOhm each in line and the thermal sum current of 12 A distributed over 6 channels in case of XPSECME gives a maximum heat dissipation 4,8 W in the output channels of the XPSECME.
Initial contact resistance is below 15 mOhms, which results in much lower dissipation of 1,1 W resp. 0,7 W (values for the circuit breakers were given for new contacts).
Thus the actual dissipation depends on load and wear conditions of the contacts.
Another important factor for heating of the relays is arcing and, in case of arcing, switching frequency.
Given calculation is valid for use that can be assumed static and no arcing.
The dissipation in the outputs add to the power consumption of the module given in the data sheet.
What would cause the ATV930 process drive to get a precharge capacitor fault?
ATV930 process drives
DC bus tie with another drive
In a configuration where the drive is connected and supplied by another drive
via the DC bus, set DCBS parameter (Generic Functions/DC-Bus Ref Link
) to "Drive with REC
" as shown in the attachment. This will avoid "Precharge Capacitor" faults due to power supplied direct to the DC bus.
[Complete settings] -> [Generic functions] -> [dbS] -> [dCbS] -> [Drive with REC]
More details can be found on page 441 of the ATV900 Programming Manual:
: the ATV600
series is not designed for applications where the DC bus is powered from an external DC source.
Cannot enable SSL HTTPS port 443 communication on ISX Central 3.0.1, 4.0 or 4.1
InfraStruXureCentral version 3.0.1, 4.0 or 4.1
If no SSL certificate is installed, SSL communication cannot be activated on the ISX Central interface
Enabling the checkbox SSL (menu Tools -> Server Administration -> Server settings -> Server access -> HTTPS port 443 -> enable) on the ISX Central console will lead to rebooting the device without any changes taken. After the reboot the box will be unchecked again, no SSL functionality will be given.
In order to establish communication via SSL, a certificate must be existent in the ISX Central device.
Check on the ISX Central console in menu Tools -> Server Administration -> Server settings -> Server security -> Secure Sockets Layer (SSL) for an existing certificate. If the original APC-MGE certificate has been removed, a self-signed certificate needs to be issued and uploaded into the unit. APC-MGE does not provide the certificate once it has been removed from the unit. You will find help on how to create a self-signed SSL certificate on the internet, since this is depending on your specific needs and what type of certificate you want to use - APC-MGE does not offer a tool to create such a certificate
HTTP and HTTPS Allowed Port Values for PowerChute Network Shutdown
PowerChute Network Shutdown
All supported OS
The allowed values are:
80 or 3052 (when HTTP is selected)
443 or 6547 (when HTTPS is selected)
5000 - 32768 (when either HTTP or HTTPS is selected)
For Xantrex branded products, they are supported locally by Xantrex's authorized distributor, Advance Trident.
Advance Trident ltd (ATL)
173 Marua Road
Mt Wellington, Auckland 1051
PO Box 4174
Phone +64 9 845 5347 ext 2
Head Office Sales: +64 9 845 5347 | South Island Sales: +64 27 449 0033
Note: Although Xantrex is owned by Schneider, they treat it separately. That's why they have an authorized distributor in NZ.
Wants to order the ATS01N230LY, ATS01N244LY, ATS01N272LY or ATS01N285LY
ATS01, Altistart 01, High HP
The launch of the ATS22 in 2011 caused the High HP units to become redundant.
The ATS01 High HP units were replaced with the ATS22 units. These are functional replacements only. The ATS01 had no overload protection, an internal power supply and simple dial adjustments. The ATS22 will require external 120V or 230V power. There are no dials to adjust, but the unit will need to be programmed. See the ATS22 User Maual, document BBV51300 to review the wiring, dimensions and programming.
ATS01N230LY - 32A rated. Replaced by ATS22D32S6U
ATS01N244LY - 44A rated. Replaced by ATS22D47S6U
ATS01N272LY - 72A rated. Replaced by ATS22D75S6U
ATS01N285LY - 85A rated. Replaced by ATS22D88S6U