Frequently Asked Questions
There are two methods to obtain your Club Clipsal number, they are:
Login to my Clipsal Electrician Portal to view your status. (this includes status, membership number, length of membership, Generator Points)
Escalate to the Club Clipsal Team on 1800 244 414 or email@example.com
No it doesn't come with a back plate. You will need a 413NP
Some of the key features are:
- For the use of cable ties for cable clamping
- Not suitable for 414/4P
- For 410, 413 and 414 products
- AS3100, AS/NZS3112, AS3109 Certified
For further information please visit https://www.clipsal.com/Trade/Products/ProductDetail?catno=413NP
What is the altitude derating for a TeSys D-Line contactor?
Digest 177 Section 18 : Contactors and Starters, IEC
North American Products
The contactors are fully rated up to 3000 meters. Following are derating multipliers for altitudes above 3000 meters for both voltage and current:
3500m x 0.90
4000m x 0.80
4500m x 0.70
5000m x 0.60
3500m x 0.92
4000m x 0.90
4500m x 0.88
5000m x 0.86
For example, an LC1D80 at 5000 meters:
- The maximum rated operational voltage is 1,000V (IEC947-4) and 690V (UL/CSA). At 5000 meters it becomes 1000V x 0.6 = 600V (IEC947-4) and 690V x 0.6 = 414V (UL/CSA).
- The maximum rated operational AC3 current is 80A. At 5000 meters it becomes 80A x 0.86 = 68A.
Proper Formats for Phone Numbers When Using Send Wireless SMS Message Alert Action from Netbotz appliance.
NetBotz version 2 using sms.
When using the Send SMS Message alert action, the GSM phone number of an alert recipient can be entered in the local format or in international format.
Example of local format when a NetBotz appliance is configured to send SMS to a GSM phone number within U.S.:
Where 512 is a U.S. area code.
Example of international format when a NetBotz appliance in U.S. is configured to send SMS to a GSM phone number in Australia:
Where 61 is the Australia country code, 414 is an area code, and + sign must be used to indicate that it is in international format.