No it doesn't come with a back plate. You will need a 413NP
Some of the key features are:
- For the use of cable ties for cable clamping
- Not suitable for 414/4P
- For 410, 413 and 414 products
- AS3100, AS/NZS3112, AS3109 Certified
For further information please visit https://www.clipsal.com/Trade/Products/ProductDetail?catno=413NP
Yes part number 413 is available in Black.
Diameter for part number 412 is 47mm.
No, we don't have an offer for the socket
The diameter for part number 412 is 47mm.
Proper Formats for Phone Numbers When Using Send Wireless SMS Message Alert Action from Netbotz appliance.
NetBotz version 2 using sms.
When using the Send SMS Message alert action, the GSM phone number of an alert recipient can be entered in the local format or in international format.
Example of local format when a NetBotz appliance is configured to send SMS to a GSM phone number within U.S.:
Where 512 is a U.S. area code.
Example of international format when a NetBotz appliance in U.S. is configured to send SMS to a GSM phone number in Australia:
Where 61 is the Australia country code, 414 is an area code, and + sign must be used to indicate that it is in international format.
What does the 412 suffix mean on the ATV312 drives?
Cannot find source in the USA
Suffix 412 indicates a special ATV312 for solar photovoltaic applications.
It is not marketed in the USA. Please contact your OEM for suggested replacements.
Levco are the suppliers of Hospitality cards +64 9 444 0161
The card is not supplied in the PDL626N pack.
The ambient operating temperature for a M251 or LMC058 controller is: -10 to 60 degrees C (14 to 140 degrees F) for horizontal installation or -10 to 50 degrees C (14 to 122 degrees F) for vertical installation.
Clipsal Socket part number - 410
The part number for the ProWorx 484 Programming Software is 771SPU6600E4DEV (ProWorx 484 Online & Offline Programming).
*** For price and availability send an email to Service.Sales@Schneider-Electric.com ***
Legacy KB System (APS) Data: RESL212362 V1.0, Originally authored by RoAl on 08/26/2013, Last Edited by RoAl on 08/26/2013
Related ranges: ProWORX
The cable pin out for a AS-W180-008 is:
The replacement for the LC1D1810 at 415 volt is the LC1D18N7.....comes with 1 N/O and 1 N/C auxiliary already fitted as standard.
Customer wants to uninstall the Control Expert Version V14 from his PC
Control Expert V14 ( former Unity Pro )
Microsoft Windows 10 Pro
Version 10.0.17134 Build 17134
- Uninstall Control Expert V14.0 from control panel.
- In the computer delete the content of the following folders:
- C:\ProgramData\Schneider Electric\Control Expert
- C:\ProgramData\Schneider Electric\CommonControlExpert
- C:\Program Files (x86)\Schneider Electric\Control Expert
- In the registry editor delete the following keys:
- HKEY_LOCAL_MACHINE\SOFTWARE\Wow6432Node\Schneider Electric\Control Expert
- HKEY_LOCAL_MACHINE\SOFTWARE\Wow6432Node\Schneider Electric\Control ExpertConfCatalog
- HKEY_LOCAL_MACHINE\SOFTWARE\Wow6432Node\Schneider Electric\Control ExpertTypesLibrary
They are both Quantum AC output modules. The difference is the voltage and grouping.
140DAO84010.....24-115 VAC, 16 isolated channels.
140DAO84210.....100-230 VAC, 4x4 grouped channels.
For discrete IO modules, you can have up to 488 digital IO counts.
For Analog IO modules, you can have up to 114 analog IO counts.
The PDL 58 is obsolete, there is no direct replacement.
Reaching end of travel limit switches will always result in a stop of motion and the respective alarm code being displayed.
This behavior is firmware related and can not be modified.
There are no provisions to change this behavior.
When Lexium 23 reaches the end of travel limit swiches it responds by stopping motion and displaying alarm 014 or alarm 015, depending on the direction of travel when reaching the limit switch.
To recover from this event you must reset the alarm and then create movement in the opposite direction of the limit switch that has been reached.
Issue: What is the maximum ambient temperature that the ATV28 can operate at?
Product Line: ATV28
Resolution: +14 to +104 F (-10 to +40 C) without grey tape removed
+14 to +122F (-10 to +50C) with grey tape removed
The Matrix-UPS does not charge its batteries in bypass mode. It is imperative to get the unit back to an online mode in order to achieve optimal functionality and keep the batteries from discharging over time. Should the Matrix need to be in bypass the battery packs should be disconnected from the Electronics Unit.
The SyMax Model 400 processor, which includes model types SCP401, 423, 424 and 444, contains 4000 on-board registers. This is the maximum number it is capable of addressing.
Product Line: ATV312
Environment: Part numbers ending in 410
Resolution: This is a custom modified version of the ATV312 that is only sold to the customer who had it customized.
A standard ATV312 will not work in it's place. It has to be ordered through the OEM.
Procedure to optimize a VJD V4.4 application :
Running the same application for Vijeo-Designer 4.4 requires about 800 KB more DRAM memory than 4.3 on XBTGT1000 and all XBTG Series targets.
This could be a problem for customers using XBTG in 4.4 because the runtime could crash with a Memory Allocation Error at some point.
XBTGT2000 Series targets and up should not experience this problem because their DRAM memory is at least twice the size of that on XBTG Series targets.
R&D is currently working to have the memory requirement for running 4.4 reduced to what was needed for 4.3.
The fix should be available in the next patch release (Vijeo-Designer 4.4 patch A).
However, before the fix is available, a short-term solution for customers wanting to upgrade to 4.4 is required.
The procedure for doing this is as follows :
See attached file : procedure to optimize a VJD V4.4 application.
(Removed File URL: 179071_C53E/optimisation_appli_V4.4_eng.doc)(Removed Image URL: /PubResEXPORT.nsf/2b87ee90be777fc085257c28006ee4ef/f01c527ac170cab9c12571b60032864b/fl_block_5/0.13D6?OpenElement&FieldElemFormat=gif)
Legacy KB System (APS) Data: RESL179071 V1.0, Originally authored by on , Last Edited by on
Related ranges: Vijeo Designer
When importing a Taylor 484 program using ProWORX 32, the descriptors do not get imported. In order to get the descriptors into the new ProWORX 32 Project, you need to export them as a Taylor ASCII file using the Taylor 484 Utility and then import them into ProWORX 32 using the "Import Documentation" function.
Note: Proworx software is obsolete and upgrading the hardware and the software to Unity Pro and either the M340, M580, or Unity Momentum, for more information contact your local distributor or Schneider Electric Sales office.
Product Line: 410, Single axis servo positioner
Resolution: There is no direct plug-in replacement for the 410 family of single axis servo positioners. Migration to Lexium 32 series drives is the general recommendation. Regardless of whether the 410 drive is used in a standalone application (or) is a remote drop on a PLC, a Lexium 32M drive may be used as replacement. 410-2 being a 10 A drive (continuous current), a LXM32MD30N4 would be an ideal replacement. If the existing motor is deemed compatible, then a resolver option card may be used to commutate the existing motor. If the 410 drive is used as a remote drop on a PLC exchanging data, an Ethernet option module may be used for communication with the PLC over Modbus/TCP.
Application specific information would be required for a more accurate listing of replacement parts.
Yes, the USB companion driver is bundled with the software.
Legacy KB System (APS) Data: RESL168244 V1.0, Originally authored by on , Last Edited by on
Related ranges: PL7
The 15 A through 150 A breakers have the AL150HD lug that will accept wire sizes of #14 through 3/0 Al or Cu. The lug kit comes with 3 lugs.
Yes, we do have a weatherproof junction box. The part number that best meets this description would be the 56JB1 then dash colour code.
Some of the key faetures are:
- Surface mount
- 1 gang
- Dimension: 91 mm Height x 101 mm Width x 101 mm Depth
- Screw on fastening
- Screwed cover attachment
- IP66 international protection rating
For further information please visit https://www.clipsal.com/Trade/Products/ProductDetail?catno=56JB1
What is the COMAND and CONTROL selections in the ETZ 410 version 1.7 used for.
The TSX ETZ410 version 1.7 web page menu functions 'COMMAND' and 'CONTROL' are only used when the connected device has the capability to use these functions. The instructions for using these functions can be found in the assocaited user manual for the attached device (i.e., Ativar 71). These functions are not supported on Premium devices (i.e., ETY, ETZ, etc.).
Follow the procedure below for changing a register value in the ProWorx 484 software.....
1 - Hit <F1> or <D> key.
2 - Hit <Alt-D> on keyboard (this opens the Holding Register Data Entry window).
3 - Type in register address and hit the <Enter> key.
4 - Make changes to the register value and save changes.
The replacement part numbers are PC-0984-351 and PC-0984-455.
Symmetra LX can automatically adjust to input voltage between 200 and 240 volts. No change to the system is required to accommodate these voltages. However, it is best practice to set the output voltage and frequency to match the input voltage and frequency. This will help avoid problems with bypass operation of the UPS. These changes can be made via the front display or the network management card.
MBP_MSTR Unit ID location
MBP_MSTR function required location of the Unit ID value.
Quantum , Momentum PLC
The MBP_MSTR function requires that the Unit ID location be in low byte of 5th word of control block.The Unit ID would refer to the unit's Modbus address.
Are replacement AC coil available for CAD32 and CAD50 relay?
Volt = coil part number
12 = LXD1J7
21 = LXD1Z7
24 = LXD1B7
32 = LXD1C7
36 = LXD1CC7
42 = LXD1D7
48 = LXD1E7
60 = LXD1EE7
100 = LXD1K7
110 = LXD1F7
115 = LXD1FE7
120 = LXD1G7
127 = LXD1FC7
200 = LXD1L7
208 = LXD1LL7
220/230 = LXD1M7
230 595 21 LXD1P7
230/240 = LXD1U7
277 781 30 LXD1W7
380/400 = LXD1Q7
400 = LXD1V7
415 = LXD1N7
440 = LXD1R7
480 = LXD1T7
600 = LXD1X7
690 = LXD1Y7
The recommended maximum torque for the screws on the TSX Momentum 170XTS00100 connector is 4.4 in/lb (0.5 Nm)
Legacy KB System (APS) Data: RESL212137 V1.0, Originally authored by RoAl on 07/24/2013, Last Edited by RoAl on 07/24/2013
Related ranges: Modicon Momentum
HD SS Accessory
Wire range of terminals
The Electrical Interlock Kits use either the 9007AO1 snap switch (1NO/1NC contacts) or 9007CO3 snap switch (2NO/2NC contacts). The terminals provided on these snap switches accept #22 - #14 AWG wire.
0.25 kW at 415 V AC 50/60 Hz
0.25 kW at 380...400 V AC 50/60 Hz
0.12 kW at 240 V AC 50/60 Hz
0.12 kW at 220...230 V AC 50/60 Hz
Reason for substitution: end of life
Substitution date: 30/12/2009
This product is replaced by:
LC1D40AN7 - TeSys D contactor - 3P(3 NO) - AC-3 - <= 440 V 40 A - 415 V AC 50/60 Hz coil
If you have a product enquire on the Generator Reward Website you can contact the Accumulate Fulfilment Team 1300 135 415 If the customer is still not receiving enough information ESCALATE to Stav Angelopoulos
If you have purchased a product online, please make sure you provide your confirmation number then you can contact the Accumulate Fulfilment Team on 1300 135 415 or email email@example.com If the customer is still not receiving enough information ESCALATE to Stav Angelopoulos
140CRA211xx DIO Adapter power supply warning
140CRA211xx DIO Adapter power supply warning
The purpose of the Warning, is because the 140CRA211xx DIO Adapter has its own built in power supply.
You are cautioned to "DO NOT WIRE THE DIO ADAPTER POWER CONNECTOR WHEN BEING USED THIS WAY"
The two power supplies it can be used with are the 140 CPS 114 00 & 140 CPS 124 00. When the 140CRA211xx DIO Adapter is used with an 8 amp power supply is will consume approximately 0.5 amps.