The new PowerTag A9 P63 & A9 F63 are supported by Smartlink Firmware from version V 2.2.0 + Ecoreach version V2.7.X
Update your Smartlink and Ecoreach version using Ecoreach software
Yes. Part number 343 is standard as 2 way.
We are no longer agents for the Goldair range. You can contact SSM (Specialised Sales & Marketing) 0800 963 963
There is no direct replacement for the SS165/15/2
The closest product to the SS165/5/2 is the 362 and 363 series of surface switches
For more information please visit the Clipsal web site on the links provided .
One possible solution would be to stick an adhesive cable tie mount to the side of the PowerTag and attach the cable tie to the neutral power wire.
Overall dimension of 651A2-BK is 365 (W) x 209 (H) x138(D).
No, unfortunately there is nothing available.
Schneider Electric has carried out tests for heating and mechanical compatibility with the products covered by the selection guide (CA908058).Schneider Electric is not able to conduct these tests for all products on the market.
The other possibility is to use the PowerTag A9 F63 version while ensuring the compatibility of the electrical connection.
Are the ATV Process and ATV Machine drives conformal coated?
Altivar Process (ATV6x0 and ATV9x) withstand to harsh environments:
- Chemical class 3C3 conforming to IEC/EN 60721-3-3.
- Mechanical class 3S3 conforming to IEC/EN 60721-3-3.
- Altivar Process ATV630C22...C31N4 drives are certified as chemical class 3C2 and mechanical class 3S2 conforming to IEC/EN 60721.
- Altivar Process ATV930C22...C31N4 drives are certified as chemical class 3C2 and mechanical class 3S2 conforming to IEC/EN 60721.
Altivar Machine (ATV320 and ATV340) withstand to harsh environments:
- Chemical class 3C3 conforming to IEC/EN 60721-3-3.
- Mechanical class 3S2 conforming to IEC/EN 60721-3-3.
However, in all cases, there are no published certificates that we can send out.
No impact on energy measurement
You must choose the register type to be Single Holding Register (R03 / W06).
We do not have a 700VA Fan speed controller.
The blade terminal of the PowerTag A9 F63 has been designed so that it does not generate any mechanical interference with the power wire, regardless of the type of cable (flexible / rigid) and the preparation of its end (bare / insulated crimped cable end / non-insulated crimped cable end). This blade terminal can not be considered as a crimped cable end, but it should be considered as a specifically designed electrical connection in the same way as: the connection terminals of a PowerTag M63 or P63, or the tooth of a distribution comb. When connecting the power wire to a screw terminal in accordance with the recommendations given in the installation instructions (cable type, section, stripping length, type of preparation, tightening torque, correct alignment between blade terminal and power wire), no degradation is generated by the PowerTag Flex blade terminal on the mechanical withstand and the quality of the cable connection.
A customer would like to know if PME 8.x is compatible with MS Office 365.
Currently PME 8.x supports Excel 2016 which is part of Office 365. This is strictly in the sense that Excel 2016 is installed locally on the server or engineering client in order to run reports. The cloud based components of 365 are not supported.
PDL no longer supplies the Thermosafe range, or any heating appliances.
255 x 362 is the cutout size for the flush mount box.
See attached pdf for more.
What does the "383" suffix represent on and ATV71....N4383 ?
Variable speed drive for synchronous motor with speed feedback
The drives are supplied as standard for asynchronous motors with or without sensor feedback.
ATV 71H075N4…HD75N4 drives can control not only those motors included in the standard offer, but also synchronous motors with speed feedback, by adding 383 at the end of the reference.
Example: ATV 71H075N4 becomes ATV 71H075N4383.
See available encoder interface cards.
Need to contact Modempak for confirmation (ph - 0800 663 367) but in theory if the mounting clip for the ducting has 84mm
centres it should fit the PDL 600 Series
The purpose of this resolution is to inform the user about an unexpected Timeout behavior of the Quantum Output module 140 DDO 364 00.
Quantum Output modules default in case of Timeout of communication to a PLC in general is Set to Zero.
Due to an incorrect default parameter of the 140 DDO 364 00, the Timeout behavior is Hold Last Value.
Affected Concept versions: Concept 2.2
To change the Timeout behavior, the user has to open the Module Parameter screen and has to leave it by the OK button. To leave it by the Cancel button will not change the Timeout behavior.
The Timeout default will be corrected with Concept 2.6SR2
Legacy KB System (APS) Data: RESL161741 V1.0, Originally authored by on , Last Edited by on
Related ranges: Concept
The part numbers for the 36W battern are BB136NEL
for a 1x36W bare battern,BB236NEL
for a 2x36W bare battern, DB136NEL
for a 2x36W diffused battern and DB236NEL
for a 2x36W diffused battern.
Some of the key features are:
- Electronic batterns and T-bar
- Reliable and energy-efficient lighting
- Polycarbonate end caps and lamp holders
- Weatherproof versions formed in Polycarbonate base and diffuser
- Colour 840 lamps included
- DALI control options available
- Range of reflectors and wire guards to suit
- End-to-end mounting possible with pre-formed cable entry punch-outs
- Large terminal blocks for looping applications
For further information please visit https://www.clipsal.com/Trade/Products/Lighting
Replacement for the S337 option.
ATV630 and ATV930
All models and serial numbers
All Altivar Process drives have the higher rated 3C3 rating as standard. This replaces the S337 option on the ATV61 and ATV71 drives.
The part name for the standalone C-Bus power supply is 5500PS
This power supply should only be used to power C-Bus hardware, and provides up to 350mA at 36v DC
Note, this power supply is not suitable for use with the CTC series touchscreens, these units have their own power supplies
The SAE_UE_MS_CDB has a fluro rating of 900VA/100uf compensated
Yes, the part name is 5753PEIRL
Issue: Can you get an Altistart ATS46 softstart with full voltage bypass?
Product Line: ATS46 8638 8639
Environment: Enclosed ATS46
Resolution: It is available with some enclosed units as an option.
With 8638 (Fusible disconnect) units or 8639 (Circuit breaker disconnect) enclosed soft starters the full voltage bypass is option Z24
This option is NOT available with 8636 (non-combination) type enclosed units.
A customer claims that their new AR8132A door handles can be opened with the standard NetShelter 333 key: W870-8135.
NetShelter SX, AR8132A
All models, all serial numbers.
The AR8132A uses a different key, but the standard 333 key will also open the lock.
The AR8132A will accept any key similar when the combination is set to the factory default of 000.
Once a new combination is set, only the key included with the AR8132A will open the lock.
No, unfortunately we do not offer a 20A version. However we do offer a 15A version which is the closest alternative. The part number is 306-*.
* = Colour code E.g. 306-BR is brown.
The letters are used to make the correspondence between the measurement of the current sensors and the voltage measurements.
If you have any doubt regarding the integrity of your system, contact Schneider Electric Customer Care Center on 1300 369 233
Yes, the material safety data sheet for the 157FSM Flexible Fire Resistant Sealant is available on request only.
To receive a copy, please call the Clipsal Technical Department on 1300 369 233.
What is the right way to connect and chain the MET 148, MSA 141, and DSM 303 accessories on the Sepam 20 or 40?
On the D Port you have to connect and chain in order:
(1) MSA 141
(2) MET 148 ( Attention: Option 2 MET 148 for Sepam 40 only )
(3) DSM 303 (Always at the end of this chain and only if no more than 2 accessories already connected on Sepam)
Note: you can't connect more 3 accessories on this chain so if you already have 1 MSA 141 and 2 MET 148 it is impossible to set also 1 DSM 303. In this case if you want to put this DSM 303, you have to remove the MSA 141 or 1 MET 148.
Key words and phrases: MSA141, MET148, DSM303
Legacy KB System (APS) Data: RESL201098 V1.0, Originally authored by DaMi on 01/22/2010, Last Edited by DaMi on 01/22/2010
Related ranges: Sepam accessories, Sepam series 20, Sepam series 40
Apple Support for NetBotz Appliances
Operating system compatibility.
The NetBotz Advanced View (and NetBotz Central Console) do not work with the Apple Macintosh Platform.
The Basic View which is pure HTML should work fine on Apple platforms.
The simulator module connector is designed to operate with the 140DAI 540 00 and the 140 DAI 740 00 modules. These modules are 115 and 230 volts AC and field wire in the same manner. If the power source was reduced to 30volts or less AC the module 140DAI 353 00 could also be used for simulating discrete inputs.