No. We have 30M35 which is 1 pole, 35A mech.
User may have purchased a 35S socket meter and needs to connect it to a 45S socket
ION8650 Series Meter
The 35S and 45S sockets are interchangeable. The ION8650 form 35S meter will function correctly in a 45S base.
Dimensions 158 x 158 x 140mm high
Unfortunately, Only 1/2 NPT is available.
286 MM Width, 258 MM height and 100 MM + wall thickness depth
210 x 158 x 112mm (L x D x W)
210 x 158 x 117mm (L x W x D)
The AC3 rating is 18.5kw, 35A
Both suits 567S Mounting Block and 558 Mounting Bracket
The part code 541ES-BK is not longer stocked in NZ
use the PDL code PDL35S 35s festoon lampholder
Issue: Does the Altivar ATV18 unit have tachometer feedback?
Product Line: ATV18
Resolution: No, it does not have tachometer feedback.
Height 158 mm
Width 120 mm
Depth 136 mm
Product weight 2.5 kg
It will accept a 3/8 size Bolt.
Customer purchased a ION 8600/8650 with "Form Factor" of 9/29/36S Base and wants to wire as a Form 35S
Installation and wiring
Customer purchased 9s meter for use in form 35S environment
It is possible to configure a form 9S ION 8600/8650 meter as a form 35S, but a form 35S cannot be converted into a 9S since
the form 35S meter does not have a blade for I2 connection.
Following the diagrams below, the meters connection terminals can be rewired to match.
The 9S meter is normally configured as bellow to accept a 3 Element 4Wire-Wye system.
As you can see, the blade inputs are used to accept the I1/I2/I3 & V1/V2/V3/Vref inputs for the 9S. A 35S meter only uses I1/I3 & V1/V3/Vref to meter the Delta system.
The 9S can be modified easily to simulate the 35S measurement structure as below:
This can be done by modifying your 9S base meter wiring as the image below:
The meter's Volts mode configuration setting, found in the Basic Setup Parameters, needs to be changed to 35S 3-Wire instead of 9S 4-Wire.
The firmware is the same for all types of form factors hence, it is not required to change the firmware.
No there is no saturn mech available. There is either the Z4061/45 cooker switch plate or the 30M35 in a Z4031VH Plate
The GT string sizing tool uses a compensating value of 35ºC above the user input temperature range.
Cell temp is always higher than ambient temp. If you've ever placed your hand on a solar panel on a sunny day, that's very evident. It's the cell temp that determines the change in Vmp, thus the need for the temperature compensation. It's our way of determining the lowest array voltage during the hottest part of the day.
The temperature difference that our calculator is using is fixed at 35C above ambient. This value was chosen based on several research reports stating that the average cell temp (above ambient temp) is 35C above ambient temp in a range of ambient temps and module mounting configurations.
Issue: What is the heat loss for the ATV31HU75M3X?
Product Line: ATV31
Cause: Watts dissipated
The total dissipated power at rated load is 388 Watts.
The part no is PDL698WH
- Worktop single switch
- Frquency rating: 50 Hz
- Suits Cat 567S mounting block and Cat 558 mounting bracket
Some customers may experience hearing a frequent clicking sound while their UPS is compensating for high input voltage.
This issue can affect SMX series Smart-UPS 1500va or less. UPS Firmware rev 3.7 or lower.
SMX750, SMX750-NMC, SMX1000, SMX1500RM2U, SMX1500RM2UNC
UPS firmware must be upgraded to 3.8 or higher
Refer to KBASE document #FA164737 to upgrade the firmware.
Netbotz SP155 readings are inaccurate with version 3.0.0 Botzware.
Upgrading to Botzware version 3.0.1 from version 3.0.0 should resolve any discrepancy in the readings of the SP155. This can be done through the Netbotz advanced view or through InfraStruXure Central.
What is the transfer time of the Back-UPS?
Back-UPS, Back-UPS PRO
Tranfer time refers to the duration in time it takes the UPS to switch from one state (i.e. Onbattery, Online...) to another.
The transfer time of the BK CS and ES units is 10-12 milliseconds.
The transfer time of the BK RS units is 6-8 milliseconds.
No unfortunately that particular switch only comes in 10A and is not removable.
However, the 4025XA has a removable mechanism and can be replaced with the mechanism 60R32 which is a 32A mechanism.
Some of the key features are:
- Saturn Series
- Extra removable switch
- Various colours available
For further information please visit https://www.clipsal.com/Trade/Products/ProductDetail?catno=4025XA
The simulator module connector is designed to operate with the 140DAI 540 00 and the 140 DAI 740 00 modules. These modules are 115 and 230 volts AC and field wire in the same manner. If the power source was reduced to 30volts or less AC the module 140DAI 353 00 could also be used for simulating discrete inputs.
Yes. The pushbutton universal dimmer 31E2PUDM is compatible with Inductive loads - 350 Watts Max.
See the attached brochure for more detail.
What is the screw size for the cover on a 9001TY1?
NEMA 1, 4, 12
Not specified in the product catalog
The screw size is 10-24 x 1 3/8
Use of Transformers with UPS systems
Applies to Low Voltage Transformers by SquareD/Schneider Electric
Output voltages of UPS systems may require changing to a more suitable level
SquareD/Schneider Electric does not recommend that standard Transformers be connected to the output of UPS systems, or at the load side of adjustable frequency motor drives. Standard Transformers are designed for a maximum of 5% total harmonic voltage distortion on the input, and the output voltage of many UPS systems and drives will exceed that maximum. For further information contact your Distributor or local SquareD/Schneider Electric Sales Office.
CTA-ID : 388
User would like to know the range of value that Arithmetic Module supports in VIP (Designer)?
ION Enterprise, StruxureWate Power Monitoring Expert 7.0.1, PME 7.2.x, PME 8.x
User would like to know the maximum and minimum range supported with Arithmetic Module within VIP.
For Arithmetic module in VIP, the data type of the output register is 64 bit floating point. Therefore, it allows a range from -10 ^ 308 to +10 ^ 308.
Is there a way to defeat or disable ground fault on a Masterpact NW breaker for primary injection testing?
Power circuit breakers
Masterpact NW circuit breakers with Micrologic trip units
There are two ways to defeat ground fault on the NW breaker for primary injection testing. You can use the Hand Held Test Kit, Cat. No. S33594, or the Full Function Test Kit, Cat. No. S33595 OR you can use the looping method to counter the single phase current during primary injection testing. See the attached Data Bulletin 0600DB9901 page 35, for looping method, or FAQ FA265488
There is a model of M340 built for harsh environments. It offers an extended temperature range of (-13 to 158 F)
In order to obtain this extended temperature capability the M340 part number requires an "H" suffix. For example: BMXP342020H.
Legacy KB System (APS) Data: RESL186036 V1.0, Originally authored by DaSo on 07/02/2007, Last Edited by DaSo on 07/02/2007
Related ranges: Modicon M340
There is no 32A mech that fits directly into the 406* plates,
The 60R32-** and 60R32COOK-** will only fit into the extra switch position on the 4025XA-**
For a standard plate with a 32A mech you will need to use a 403* plate with a 30 series 35A mech, 30M35
What is an What is an ATV31****378?
This is a special drive for Buhler Company. The 378 suffix indicates that logic input LI6 can be used as a 24vdc pulsed speed reference. Would need to obtain a replacement from Buhler Company. May also be identified as S378 suffix.
NetBotz version 1 and 2 Appliances Operating Environments
NetBotz version 1 and 2
The NetBotz Appliances and pods are designed for indoor use only.
The environmental operating conditions are as follows:
* Temperature: 35F to 120F (1.6C to 48.8C)
* Humidity: 10% to 90% non-condensing
The air flow rate for the 6600A is 338 cubic meters per hour
Unfortunately there are 2 diffrent airflow rates listed, however 338 Cubic meters is the correct output.
The En Suite is suitable for small bathrooms and en suites with ceilings of height 2.7 metres and above. The En Suite is also suited to small kitchens, toilets and laundries. Included in these neat and compact three-in-one combination units are two 275 Watt radiant heat globes, one 14W CFL central reﬂector globe and a high performance exhaust fan.
Some of the key features are:
- 264 mm Width
- Room protrusion 60 mm
- External protrusion 200 mm
- Duct size dia. (E) 200 mm
- Hole size 325 (395) x 240 mm
For further information please visit https://www.clipsal.com/Trade/Products/ProductDetail?catno=6600A
AOUT on 4203 cannot be connected directly to AIN on the SP350 because both are current sinking type of I/O.
Drawing shown below describes how AOUT on 4203DR transmitter should be connected to AIN on SCADAPack 350 when I-I Isolator is used.
Jumper for analog input on SCADAPack 350 must be in the Current position.
Serial port COM1 on the SCADAPack 350 is dedicated 2-wire RS-485 serial communication port.
Wiring diagram for SCADAPack 32 and SCADAPack 350 communication through RS-485 COM ports is shown below.
Note that jumper J9 must be installed so that SCADAPack 32 COM1 is in RS-485 mode.
This resolution describes a workaround for an effect by a Hot Standby switchover with RIO and a software counter.
The RIO cable connection to the Primary CRP 931 fails.
An input from a 140 DDI 353 00 module has value "1" at the same time.
The Standby system switches to Primary (what is correct).
But the input bit gets for a short time the value "0", because the CRA is not available while switchover.
If the binary input is linked to a software counter the counter will change the value. Also affected are program parts, which use this binary input together with Edge detection.
Problem is known with the following components:
Concept 2.6 SR2
140CPU43412A, EXEC 1.25, Kernel 1.01
140CHS11000, EXEC 1.04, Kernel 1.00
140CRP93100, EXEC 1.15, Kernel 1.01
140 DDI 353 00
It should exist with all Hot Standby systems equiped with 140CRP93100, every discrete Input and a software counter or a Edge detection is linked to the Input module.
Use the EN input of the software counter and link it to the healthy bit of the Input module. This avoids to increase the counter during RIO cable interrupt.
Legacy KB System (APS) Data: RESL167770 V1.0, Originally authored by on , Last Edited by on
Related ranges: Modicon Quantum
The SCADAPack 334 with 5607 I/O module is comprised of four types of I/O channels, digital inputs, digital outputs, analog inputs, and analog outputs.
The digital input assignment provides twenty four I/O channels for the digital input data from the SCADAPack 5607 I/O Module hardware. The digital input registers are updated continuously with data read from the digital inputs.
The 5607 I/O Module provides sixteen external digital inputs. These are externally wetted inputs.
The module provides 8 internal digital inputs, which indicate if the corresponding analog input is in or out of range.
See Configuration Example below:
Yes. the sensor head can be pulled down 30º and rotate in range of 350 º to orient at desired angle for better detection, or avoid from unwanted direction