The power supply to suit the 560125R/2 25W audio amplifier is a 5600P24H3750A.
What does the suffix 25K indicate on an MPZ device?
Mini power zone
MPZ mini power zone
The 25K suffix indicates the MPZ is rated at 25KAIC. The standard AIC is 18K. The 25K units have a higher rated 25K AIC primary main breaker installed, and so the entire unit AIC is then rated at 25K. Same for the 65K.
No, the TCP_Open requires the ETY 5103 module which is not supported by the TSX P57 2634M.
Legacy KB System (APS) Data: RESL175067 V1.0, Originally authored by on , Last Edited by on
Related ranges: Domino
Yes, it can but you will need to put a 31CAP in parallel with the load.
Netbotz and FTP Return Codes
NetBotz ftp codes
When configuring the FTP Alert Action on a Netbotz device, the FTP server may return error codes which may viewed in the Appliance Log. The return codes may be used to further troubleshoot the problem.
The return codes for FTP servers are:
110 Restart marker reply. In this case, the text is exact and not left to the particular implementation; it must read: MARK yyyy = mmmm where yyyy is User-process data stream marker, and mmmm server's equivalent marker (note the spaces between markers and "=").
120 Service ready in nnn minutes.
125 Data connection already open; transfer starting.
150 File status okay; about to open data connection.
200 Command okay.
202 Command not implemented, superfluous at this site.
211 System status, or system help reply.
212 Directory status.
213 File status.
214 Help message.On how to use the server or the meaning of a particular non-standard command. This reply is useful only to the human user.
215 NAME system type. WhereNAME is an official system name from the list in the Assigned Numbers document.
220 Service ready for new user.
221 Service closing control connection.
225 Data connection open; no transfer in progress.
226 Closing data connection. Requested file action successful (for example, file transfer or file abort).
227 Entering Passive Mode (h1,h2,h3,h4,p1,p2).
230 User logged in, proceed. Logged out if appropriate.
250 Requested file action okay, completed.
257 ""PATHNAME"" created.
331 User name okay, need password. 332 Need account for login.
350 Requested file action pending further information
421 Service not available, closing control connection. This may be a reply to any command if the service knows it must shut down.
425 Can't open data connection.
426 Connection closed; transfer aborted.
450 Requested file action not taken.
451 Requested action aborted. Local error in processing.
452 Requested action not taken. Insufficient storage space in system.File unavailable (e.g., file busy)
500 Syntax error, command unrecognized. This may include errors such as command line too long.
501 Syntax error in parameters or arguments.
502 Command not implemented.
503 Bad sequence of commands.
504 Command not implemented for that parameter.
530 Not logged in.
532 Need account for storing files.
550 Requested action not taken. File unavailable (e.g., file not found, no access). (550 a:: no such directory means no diskette in a: drive.)
551 Requested action aborted. Page type unknown.
552 Requested file action aborted. Exceeded storage allocation (for current directory or dataset). 553 Requested action not taken. File name not allowed.
286 MM Width, 258 MM height and 100 MM + wall thickness depth
The part number for the flap of 255 as a spare is 255FLAP-TR.
The maximum distance is 100m without obstructions, this is reduced to 25m if the receiver is enclosed in a metal enclosure.
The part name is A9F55325
Part number is PDL 56SW332
Is the 9001KM38 a resistor type or full voltage type of light module?
Both descriptions are accurate. They are both the same device but can be selected by either description depending on the application/preference.
Legacy Circuit Breakers
Electrical Distribution Equipment
The interrupt ratings below:
42k AIR at 240V
25k AIR at 480V
22k AIR at 600V.
A Clipsal 157 wall box will be suitable for most C-Bus switchs.
The only exception is for the C-Bus Reflection range, which uses its own specific wall box: Part name R5060WB
The part number for flap to suit 255 is 255FLAP-TR.
Yes, the 2025RCD30-WE will fit into a 255 weather protected box.The 2025RCD30-WE is 27mm deep and the 255 has 35mm depth. The bottom screwed plug will need to be shortened if not used as a cable entry.
Issue: Why is Altivar ATV16 only going to 50 hz and want 60hz maximum frequency?
Product Line: ATV16
Cause: Speed won't go above 50Hz
Resolution: Need to set TFR ( maximum freqeuncy ) for 60 and HSP ( high speed ) to 60hz.
Is a CA2KN22 available with a 277 volt AC coil ?
Tesys K IEC Style Rekays
Application is calling for 277v coil.
Yes. The voltage code is UE7. CA2KN22UE7 is currently obsolete.
Yes, the 25, Standard Series, double outlet,10A is available in the colour Blue. The part number is 25-DB.
Need the register list for my VAMP relay.
See the attached files for the VAMP 255 communications maps, this includes maps for:
Note: Latest information is available in m.vamp.fi
The aux contacts on all our contactors are rated at 10A Ith
No - the highest current rating is 25A
LC1D25BD is the correct part number
The "H" at the end of the Modicon M340 part number stands for the "Ruggedized" version. This version allows the M340 to be used in more severe environments because of the protective coating on all their circuit boards and has an extended temperature range from - 25C to + 70C.
Legacy KB System (APS) Data: RESL209489 V1.0, Originally authored by DiSa on 10/25/2012, Last Edited by DiSa on 10/25/2012
Related ranges: Modicon M340
The part number for a Din rail mount 25A change over switch is a 4PS25CO
- Maximum 4 - Isolators - DIN rail mount
- Night, off, day switching of luminaries where daylight supplements internal lighting
- Incoming and outgoing terminals are screw down type and accommodate copper conductors up to 16 sq mm
- Auto, off, manual switching of machines
- Auxiliary, off, mains switching of small stand-by generators
For further information please visit https://www.clipsal.com/Trade/Products/ProductDetail?catno=4PS25CO
Issue: Need to know the operating voltage of the Vamp 255 digital inputs.
Product Line: Vamp 255
Resolution: The Vamp 255 has 2 sets of digital inputs. Digital inputs 1-6 are internally wetted with 48Vdc. The other 12 digital inputs operating voltage is defined by the part number ordering code:
A = 40 - 265 VAC/VDC
B = 18 - 36 VDC
C = 40 - 265 VAC/VDC + ARC Protection
D = 18 - 36 VDC + ARC Protection
E = 40 - 265 VAC/VDC + D19, DI20 + ARC channel
F = 18 - 36 VDC + D19, DI20 + ARC channel
Keywords: Vamp 255, Vamp 255 digital inputs, Vamp 255 operating voltage
An EGX continues to log a device despite the User Guide suggesting it should stop after a missed interval.
EGX300 Gateway Device
EGX Data Log
The table containing 'Error Codes for Data Logs' in the User Guide (pg. 39) states "Logging is left enabled unless the last interval was missed" for error codes 19 and 25. This suggests that the EGX should stop logging data from a device after an error appears. However, as seen in the image below, an error is observed more than once and the device continues to be logged.
Since the EGX300 is an obsolete device, it is unlikely the User Guide will be updated. This article will serve as a correction for the EGX300 User Guide's wording.
For this 4RCBM series range the KA rating is above 25a is limited to 6KA and below 25amps is 10ka.
new code = A9C20736 iCT Contactor 25A 2NC AC7a rated
6A - A9FDB606
10A - A9FDB610
16A - A9FDB616
20A - A9FDB620
25A - A9FDB625
FLC1 is the parameter to enter the Motor nominal current in TeSys T. In this parameter, the Motor nominal current is entered as a percentage of the rated value of the TeSys T.
For TeSys T of range 8Amps (LTMR08) and a motor of 2 Amps nominal current, you have to set the FLC1 value to 25% because the Motor nominal current is 25% of the full load current of TeSys T Module (LTMR08).
This means that the current in register 466 (value of current in percent) take the value of 100% when you reach 25% of the current of the TeSys T Module rated current value.
You will be able to find your answer in the user manual section 6.3 ZART8L Diagnostic p 157 to 160. In fact you have a Led code.
Options are NSY3X6625 - 600 x 600 x 250 or NSY3X7525 - 700 x 500 x 250
4RC225/30 is an alternate for 4EL25/2/30, 25A , 30mA, 2 module RCD.
- Unique new white finish for a fresh modern look
- Base module = 18 mm wide, compact standardised and consistent module dimensions
- Lift-up terminals. Safer ‘no hot spot’ terminations and all cable strands are locked in
- Cable automatically guided to the correct position: terminals with guard
- Fast closure
- The presence of the green strip guarantees physical opening of the contacts and allows operations to be performed on the downstream circuit in complete safety
- Same housing as AC type MCBs. Uniformity in space requirements and installation
- Superior, safe and reliable DC breaking per pole
- Used with marine, telecommunications, solar power, emergency power, battery power
- Excellent breaking capability for its compact size
- Standard type
- 75 mm modular spacing
- Surge current protected to 250 A at 8/20 uS
- Operating temperature: -5 to 40 deg C
- Degree of pollution is 2
- Rated Impulse withstand voltage is 6 kV
The memory of M221 cannot be expanded. The M221 has the following types of memory:
RAM: 512 Kbyte, of which 256 Kbyte available for the application. It is used to execute the application and contains data
Flash: 1.5 Mbyte, of which 256 Kbyte is used to backup the user application and data in case of power outage. It is used to save the application
The SD card is only used to transfer the application or update the firmware
Trying to connect to the VAMP 200 series through the RS232 port fails.
VAMP 255, VAMP 257, VAMP 259, VAMP 200 series, VX003
Connecting to VAMP set to configure settings.
The RS232 port configuration is not a standard RS232 port.
The Multi Gang Switch Assemblies (less mechanisms) - Metal Plate Range, 30 Series Rocker Type, Switch Plate 10 Gang, 2 rows of 5 ( B10/30/5
) has facia dimensions of
257mm (W) X 120mm (H).
Some of the key features of the B10/30/5 are:
- 30 series rocker type
- Switch arrangement 5 horizontal and 2 vertical
- Fascia size: 257 mm Width x 120 mm Height
- 10 number of switch apertures
For further information please visit https://www.clipsal.com/Trade/Products/ProductDetail?catno=B10/30/5
Yes, the part number for the flap / lid is 255FLAP-TR
Part number is actually 255FLAP -TR
- If you use the READ_VAR at address 130 with quantity = 1 you will get an error : CommError = 254 and OperError = 3.
- If you change the quantity = 2 you will still get the same error : CommError = 254 and OperError = 3: You will get the high order byte in %MW130 = 0 and lower order byte in %MW131 = 0.
The general register list for the Power meters gives you the Jbus addressing registers and not the Modbus addressing registers.
Jbus addressing starts a n and the Modbus addressing then should be n -1.
- If you now use the READ_VAR at address 129 (n -1) with quantity = 1 you will get the same error : CommError = 254 and OperError = 3.
- If you change the quantity = 2 life is good: You will get the high order byte in %MW130 = xxxx and lower order byte in %MW131 = xxx.