Frequently Asked Questions
266MD20 - for 20mm medium duty conduit.
266MD25 - for 25mm medium duty conduit.
Yes , there is provisions for stacking on the left side of the breaker up to 54mm (3`)
CTA-ID : 2062625
No, they are light duty. Buy the 1240HL25 to obtain a heavy duty lid and gasket , or if gasket is required for retro fit then buy 1240GT
For more information on this product range please visit the Clipsal web site on the link provided
Will the new style Tesys Contactors still utilize the old style mechanical interlocks?
IEC contactors and starters
Products sold and used in the United States
Identifying product compatibility
No, it will not. Refer to the current Digest for the selection of mechanical interlock components for current style Tesys D-line contactors.
ATV212 programming to follow 0-10vdc speed signal on VIA and start/stop via terminals
Altivar ATV21 and ATV212
Wants to use VIA for 0-10vdc speed control and start stop via 2 wire control thru the terminal inputs.
SW100 switch setting: Set the switch on the main circuit board to U for an 0-10vdc input signal for VIA (set upper switch to the left position)
0-10vdc signal to VIA and CC
Two wire start dry contact or relay is wired between P24 and F
FNOD= 1 VIA
CNOD= 0 (terminal control)
F111= 2 for 2 wire control
uLu= motor voltage
F415= normal motor current
F417= normal motor RPMs
thr = normal motor current