Frequently Asked Questions
Unfortunately we dont make U entry junction box any more, closest will be 240/25/2A and similar.
We recommend using 1.5mm², 240V, mains rated, 2-core cable for the Dali line. This ensures you can achieve the maximum DALI line cable length of 300m.
In an addition to the above the polarity of DALI line must be consistent throughout each installation to prevent short circuits.
There are two main methods of configuring the DALI line and they are loop-in, loop-out or star configuration where the longest run shall not exceed 300m when using the above recommended cabling.The DALI line is typically 16V DC and must not have a voltage drop of more than 2V on the DALI line.
***Please note, other cabling can be used such as various unshielded 2-core cables as it is classified as extra-low voltage, however it is important that voltage drop calculations are taken into consideration to avoid communication issues.
For further inquiries please contact technical support on 13 73 28 (13 SEAU).