Frequently Asked Questions
As per installation instructions use a 63mm hole saw to cut holes.
What is the coil consumption or burden for the Tesys LC*D** contactors?
Tesys Contactors and Overload Relays
All AC coils for the LC1D40 through LC1D80 3 or 4-pole contactors have an inrush of 200VA for 50 Hertz applications or 220VA for 60Hz.
Sealed values are 20VA for 50 Hertz applications or 22VA for 60 Hertz applications. For 50/60 Hertz coil inrush is 245VA and sealed is 26VA
CTA-ID : 2029994
No. Unfortunately, we no longer have the high power dimmer available.
No. It is not possible. As per the attached document the NW16 have sensor rating only from 800 - 1600A, So a 2000A Sensor Plug is not suitable for NW16 Breaker. So it can not be changed.
Are M400A actuator circuit cards replaceable?
Valves and Actuator
N. The circuit cards for actuators are not replaceable. Order a complete new actuator.