Frequently Asked Questions
The part number for a plug to suit the 240/25/3 is a 220/25.
30USM-WE = Universal switch mechanism 20/16AX - compared to the 10A only 30M-WE
(see attached 30USM Brochure)
Micrologic test equipment
Electrical Distribution Equipment
Yes, the FFTK can be repaired in most cases. Have the distributor contact Customer Service for a "Return for Repair" RMA and send it back.
(see internal FA289579)
Yes. Add a D suffix to the drive part number.
ATV61HC22N4 includes a DC choke.
ATV61HC22N4D does not include a DC choke.
Note that if a DC choke is not used, a jumper wire, of sufficient current capacity, must be installed between the PA and PO terminals. A good rule of thumb is to use the same size wire that is on the DC choke for the jumper wire. Also, if the DC choke is not used, a 5% line reactor ahead of the drive is Mandatory. Failure to use a 5% line reactor ahead of the drive if no DC choke is present can result in damage to the drive that warranty does not cover.
CTA-ID : 2061651