Frequently Asked Questions
Yes, the part number is a 2015D15
Not available, but Clipsal 2015/15 is available in red but it's horizontal.
Most common issue is Parameter o19 must be set to the maximum pressure of the sensor in Bars. Parameter o20 is set to the PI setpoint in Bars.
To get the pressure in Bars, divide the pressure in PSI by 14.504.
CTA-ID : 2015151
To obtain a surge protected 15A outlet you will need to purchase a C2015/15X and a 30SFM and replace the extra switch in the outlet with the 30SFM surge protector mechanism and then wire accordingly.
For some reason we have given the 30CSFM a 10A rating. The mechanism only needs to be rated for the correct voltage and correct fault current the amperage rating is irrelevant as this device does not have the load passing through it, it is there merely for fault conditions.
Factory installation of key interlock provisions on NW Masterpact circuit breakers.
Products sold and used in the United States
Factory installed key interlock on NW Masterpact circuit breakers
It is possible to order "provision-only" for an NW breaker key interlock. The provision is also available as a field-installable kit. See pricing guide for catalog numbers.
CTA-ID : 2015133