Not available, but Clipsal 2015/15 is available in red but it's horizontal.
Yes, the part number is a 2015D15
Pumptrol pressure switches, Class 9013
Noryl SE-1X is used on 9013G devices for the cover, and on 9013F products with 3R rating.
CTA-ID : 2010510
To obtain a surge protected 15A outlet you will need to purchase a C2015/15X and a 30SFM and replace the extra switch in the outlet with the 30SFM surge protector mechanism and then wire accordingly.
For some reason we have given the 30CSFM a 10A rating. The mechanism only needs to be rated for the correct voltage and correct fault current the amperage rating is irrelevant as this device does not have the load passing through it, it is there merely for fault conditions.
Most common issue is Parameter o19 must be set to the maximum pressure of the sensor in Bars. Parameter o20 is set to the PI setpoint in Bars.
To get the pressure in Bars, divide the pressure in PSI by 14.504.
CTA-ID : 2015151
Issue: What is the replacement part number for the SCR module for ATS23C15N or ATS23C24N?
Product Line: ATS23
Environment: ATS23C15N ATS23C24N
Resolution: No parts available replace starter
Issue:Cooling Fan part number
Environment: Replacement parts
Cause: Cooling fan failure.
Resolution: See attached document for heat sink cooling fan part numbers.
Are Masterpact circuit breakers 100% Rated?
Masterpact NT and NW
NEMA influenced markets only
All UL 489 listed Masterpact NT and NW circuit breakers are 100% rated.
Note that standard 80% vs. 100% rating applies to breakers listed per UL 489 only.
Issue: Why does the ATV28 unit not output the proper voltage when trying to test drive unloaded?
Product Line: ATV28
Cause: Outoput voltage
You can not test this drive with no motor connected to the output terminals because it is a current driven device.
Would not expect to see appropriate values corresponding up to rated line voltage at high speed because of design of unit, regardless of what torque type have unit set for in Uft menu.
Issue: How do I assign Reference Switching to a Logic input in the ATV28?
Product Line: ATV28
From factory I/O settings it will be necessary to set the LI4 then LI3 inputs to some setting that is compatible with Reference Switching. Preset speeds are incompatible with Reference Switching. LI4 must be changed before LI3. If not using LI3 or LI4 set them to NO.
In the I-O menu change the desired logic input to rFC. It will be in Auto and use AI2 or AIC for speed reference when the contact is open. The drive will be in Hand mode and use AI1 for speed signal when there is 24 VDC on the rFC input.
Coil consumption or burden for the Tesys LC1D/2D contactors from 9A - 38A
Contactors and Starters - IEC
North American Products
All AC coils for the LC1D09 through LC1D38 3-pole contactors ( including ring tongue, quick connect and spring terminal versions ) have an inrush of 70 volt-amps for either 50 or 60 Hertz applications, and a sealed value of 7 volt-amps for 50Hertz applications or 7.5 volt-amps for 60 Hertz applications.
What are the Square D part numbers for the fans used internal to the ATV66D33N4U?
Each of these drives have the VZ3V665 heat sink fan which is the larger fan located in the bottom of the unit. The NMB part number for this fan is 5915PC-23T-B30.
Each of these drives have the VZ3V6654 power board stirring fan which is a small fan located in the upper left side of the unit.
Only the ATV66D54N4U, ATV66D64N4U, ATV66D79N4U and ATV66D46M2U drives also have a VZ3V6655 capacitor bank fan located above the power terminal block.
These drives are the Frame Size 4 and Frame Size 5 ATV66.
The part numbers are listed on page 98 (page 104 in Adobe Acrobat) of the VD0C06S304E Receiving, Installation and Sart Up manual in Appendix A - Spare parts list. The part # for the fans of the other size units is also listed in this table.