The part code is A9C30211
Wall clip - 2154H2
Wall Bracket - 2155PHRM2
Wall Box - 2157H2
Use a 2154H2 ( wall clip) , 2155PHRM2 ( plaster mount bracket ) or 2157H2 ( Wall box) recessed 8mm
for more information on this product range please visit the Clipsal web site on the link provided
The separator part code is 27001
The mains switch is 15092
The part name is as follows: 2157H2
Yes you can it has 2x84mm mounting centers. Or you can use the 2154H2 mounting bracket or the 2157H2 Metal wall box.
The mounting centers of the 3155H4 mounting bracket is 179.8mm.
Part number 15222 is no longer available the alternative is the A9A15222.
Please use link for Data sheet:
Use a 2157H2
or a 2154H2 mounting bracket
The part number for bracket to suit is 155P.
The largest transformer that we have is 63VA - The part code is 15222
A9C30831 is the Acti9 code for the 1P 1NO 32A 230v AC impulse relay.
205mm x 395mm x 155mm (H x W x D) excluding the handle.
Overall depth with standard handle is 213mm.
The 154/2 is the clip to suit any Prestige large format plate 115mm x 115mm
The dimensions are 121mm (W) X 83mm (H) X 155mm (D).
The part number is 3155H4 at this stage anticipated release is December 2016.
Part number 156/2 can be used on all Prestige large format plates.
The difference between the Surge Arrester references 15597 and 16447 is as follows:
1.) 15597 is a PF20 3Pole Fixed type Type 2 LV Surge Arrester.
2.) 16447 is a PRD20 3Pole Withdrawable type Type 2 LV Surge Arrester.
Both are suitable to be used in low risk level and for use in TNC Earthing systems.
The difference is that 15597 at its end of life needs to be replaced as it is Fixed type, while 16447 at its end of life can be reused by simply replacing the cartridge as it is Withdrawable type, and the other major advantage is that the wiring does not get disturbed.
Will the 9001KA contact blocks work at 24VDC?
9001 KA1-KA6, KA21-25, KA31-35, KA1G-KA6 contact blocks will work on 24VDC providing the do not exceed 1.1amp make and break nor exceed 10 amps continuous current.
CTA-ID : 15554
Standard 2 gang flush box will suit - part number 157/2
PDL56TC24HB - Mechanical Synchronous, 1 channel, 15 min switching min 150hr Backup
PDL56TCU - Digital Quartz, 10yr Bat.Backup, 1 channel, 20 storage spaces
The 2157H2 is used on both standard Saturn & Saturn Zen
What are the replacement leads for a 6610VT1 Wiggy voltage tester?
Obsolete voltage testers formerly sold by Square D Company.
Wiggy voltage testers
The 6610VT1 voltage test and all related accessories are now obsolete with no replacement. Consider another manufacturer of similar devices.
You can direct mount onto the lid of the 80 or 155mm trunking or use the ISM15150
Other options are the Unistrut 2087016 and adaptors can also be found at cccutting.co.nz
The part number for the wall clip suitable for large format Prestige P2000 plaes is 154/2.
A System ID register located at addresses 30 (Integer) and 315 (Float) exists within the Enercept Meter. Reading that register will yield one of two values:
A value of 15022 will be returned from the Enhanced Enercept model.
A value of 15023 will be returned from the Basic Enercept model.
What is the baud rate for ATS48 modbus?
Need to use 115.2 baud
ATS48 modbus is only available at 19200 or 9600.
Please note that the remote HMI only works with the 19200 baud rate.
There are two options available and they are both DIN rail mount which will fit into a 56CB4.
- Part number: 15202 - This unit is a "direct connect" device and is rated up to 10A and it is 2 modules wide.
- Part number: 15209 - This unit uses C/T Clamps to measure the current and is rated from 0-5000A and it is 2 modules wide. (clamps not included)
For further information please visit https://www.schneider-electric.com.au/en/product-range/994-digital-amp---vlt--fre/
What is the Current Gain Board part number for an ATV58HC23N4 and ATV58HC28N4 ?
ATV58HC23N4 and ATV58HC28N4
ATV58, All serial numbers
The part number is VX5A38C15. Obsolete no replacement part.
Does Schneider Electric have any Altivar drives that do regeneration?
Altivar Process 980 Regeneration Drive
The Active Front End (AFE), Altivar Process 980 Drive system is a packaged, high-performance solution for regenerative applications. This regenerative drive is highly efficient in four-quadrant technology for speed control in both directions. The horsepower range is 150hp - 900hp.
No unfortunately there is no wall box to suit 3015/4 ICONIC quad outlet.
The only mounting accessory available for the 3015/4 is a 3155H4 which is a stud bracket.
For further information on our product range please visit Trade - Clipsal by Schneider Electric
Issue: Cannot establish communications via USB with the SMT or SMX UPS after installing PowerChute Agent.
PowerChute Business Edition
All supported OS
USB cable not connected during software installation
If you installed the PowerChute Agent without the USB communications cable connected to the UPS, then you cannot subsequently establish communications. You need to correctly connect the USB communications cable from the computer to the UPS and then re-install the Agent.
If the USB cable was connected during installation please review knowledge base document FA163608
PowerChute Personal Edition 3.X "has stopped working" on Windows Vista or Windows 7.
PowerChute Personal Edition version 3.X
All supported Windows OS
If you see "PowerChute has stopped working" on Windows Vista or Windows 7
the reason is missing Arial font/s on your system. To check to see if Arial.ttf and or Arialbd.ttf are missing look in C:\Windows\Fonts\Arial
If they are missing you can load the Arial fonts - font family from you system CD, system back-up drive, or back-up CD. You may also download the fonts from Microsoft.com