Frequently asked questions
Is it possible to defeat or disable ground fault on Masterpact NW with Micrologic 6.0A for primary injection testing?
28 September 2021Issue:
Is there a way to defeat or disable ground fault on a Masterpact NW breaker for primary injection testing?
Power circuit breakers
Masterpact NW circuit breakers with Micrologic trip units
There are two ways to defeat ground fault on the NW breaker for primary injection testing. You can use the Hand Held Test Kit, Cat. No. S33594, or the Full Function Test Kit, Cat. No. S33595 OR you can use the looping method to counter the single phase current during primary injection testing. See the attached Data Bulletin 0600DB9901 page 35, for looping method, or FAQ Looping Method for Testing Breakers with Ground Fault Trip Units