23 January 2021
Micrologic Power or Harmonic trip unit won't let me change the on-screen settings. What is the problem?Product Line:
5.0P, 6.0P, 5.0H, 6.0HResolution:
The trip unit settings cannot be adjusted via the menu buttons on the trip unit screen unless the switch cover is OPEN.