23 January 2021
PT100 probe to measure temperature
ATV61 and ATV71
All models and serial numbers
No, LI6 is a digital input and cannot read a resistance or an analog value. LI6 can be used in conjunction with a PTC. The input is activated when the resistance of the PTC reaches 3k ohms.
It is not designed to accept a PT100 probe.
ATV630 can do this.