28 September 2021
Needs to run a 3 phase motor with 1 phase input voltage.
Customer only has single phase input power but needs to run a 3 phase motor.
Several of our drives have been tested and approved to accept single phase input power to run 3 phase motors.
Drives must be derated to handle the increased current on the input bridge and increased ripple or noise on the DC Bus.
In some cases input line reactors may be required or may allow higher SSCR ratings.
Consult the appropriate Quick Start Guide Annex. These documents also provide fuse and circuit breaker information.
Only recommended on single phase for pump application (Altivar Process Drive) : https://www.schneider-electric.com/en/download/document/EAV64300/
Not currently approved for use on single phase applications.
(Constant or Variable Torque applications): https://www.schneider-electric.com/en/download/document/NVE21777/
Not currently approved for use on single phase input applications
(Constant or Variable Torque applications): https://www.schneider-electric.com/en/download/document/S1A58684/
The ATV212 is not capable of supporting single phase input applications.
For any other application requirements consult following 3rd party website (Bonitron).
The ATV930 product is recommended for use with this option.
Contact Bonitron directly for assistance.
OLDER product info:
NOTE- product has been discontinued (Variable Torque applications):https://www.schneider-electric.us/en/download/document/S1B86981/
NOTE - product has been discontinued (Constant Torque applications):https://www.schneider-electric.com/en/download/document/S1B86988/
NOTE - product has been discontinued (Constant or Variable Troque applications):https://www.schneider-electric.us/en/download/document/S1B16328/
NOTE - product has been discontinued (Constant or Variable Troque applications) :https://www.schneider-electric.com/ww/en/download/document/S1B39941?showAsIframe=true